Main range of productOsiSense XS series nameGeneral purpose sensor typeInductive proximity sensor product specific application- sensor nameXS7 sensor designForm 12 x 40 x 26 size26 mm body typeFixed enclosure materialPlastic type of output signalDiscrete wiring technique4-wire [Sn] nominal sensing distance2 mm discrete output function1 NO or 1 NC programmable discrete output typePNP electrical connectionCable cable length5 m wire insulation materialPVC [Us] rated supply voltage12...48 V DC switching capacity in mA<= 200 mA with overload and short-circuit protection IP degree of protectionIP67 conforming to IEC 60529 Complementary detection faceLateral detector flush mounting acceptanceFlush mountable materialPlastic front materialPlastic operating zone0…1.6 mm differential travel3...20% of Sr repeat accuracy<= 10% of Sr output circuit typeDC cable composition4 x 0.34 mm² status LEDOutput state: 1 LED (yellow) supply voltage limits10…58 V DC switching frequency<= 2000 Hz maximum voltage drop<2.6 V (closed) current consumption0...10 mA no-load maximum delay first up4 ms maximum delay response0.5 ms maximum delay recovery1 ms markingCE depth26 mm height40 mm width12 mm Environment product certificationsCSAULCCC ambient air temperature for operation-25…70 °C ambient air temperature for storage-40…85 °C vibration resistance25 gn amplitude = +/- 2 mm (f = 10…55 Hz) conforming to IEC 60068-2-6 shock resistance50 gn for 11 ms conforming to IEC 60068-2-27 Offer Sustainability EU RoHS DirectivePro-active compliance (Product out of EU RoHS legal scope)
EU RoHS Declaration
Mercury freeYes RoHS exemption information Environmental Disclosure Circularity ProfileNo need of specific recycling operations
End of Life Information
Contractual warranty Warranty18 months
CertificateFormatSizeAdd to My DocumentsInstruction sheetFormatSizeAdd to My DocumentsDeclaration of conformityFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
- All Languages7
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.