Preventa safety remote output discrete module - 16 O not isolatedShow more characteristics >
Main range of productPreventa Safety automation product or component typePreventa safety remote output discrete module safety module nameXPSMF2 safety module applicationExtension of I/O capacity safety use categoryCategory 4 maximum conforming to EN 954-1Performance level e conforming to EN/ISO 13849-1SIL 3 conforming to EN/IEC 61508 function of moduleMonitoring safety actuatorsMonitoring safety dialogue [Us] rated supply voltage24 V DC (- 15...20 %) supplySELV or PELV conforming to EN/IEC 60950 discrete output number16, not isolated structure type10BASE-T/100BASE-TX Complementary response timeDepending on size of application associated fuse rating10 A, slow-blow discrete output current<= 1 A at 40 °C (per module)<= 16 A at 60 °C (per channel)<= 2 mA inductive load500 mH tungsten load10 W / 1 A25 W / 2 A leakage current<= 1 mA, at 2 V at state 0 communication port protocolSafe Ethernet with 2 RJ45 port(s), transmission rate: 100 Mbps, 10 Mbps, medium: dual twisted pair cable, category 5D or better exchange modeHalf duplex, full duplex, autonegotiation number of terminal blocks1 for output circuit1 for power supply4 for discrete output current consumption0.2 A at 24 V DC on power supply mounting support35 mm symmetrical DIN rail depth86.5 mm height109 mm width207 mm product weight0.85 kg Environment IP degree of protectionIP20 ambient air temperature for operation0...60 °C ambient air temperature for storage-40...85 °C Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
User guideSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.
PresentationHousing ElementsFront View
Power supply input
IndicatorsTop ViewBottom View
Dimensions DrawingsDimensionsFront ViewSide View
Mounting and ClearanceMountingMinimum ClearancesAir Circulation
The height of the cable ducts is less than 40 mm / 1.57 in.
The height of the cable ducts is greater than 40 mm / 1.57 in.
L = H - 40 mm / 1.57 in.
L = length of the spacer
H = height of the cable duct
Minimum clearance when H > 40 mm/1.57 in. and no spacerMounting Precautions Relating to RJ45 Connector(1)minimum value