Main range of productPreventa Safety automation product or component typeSafe relay output module device short nameXPSMCM electrical connectionSpring terminal [Us] rated supply voltage24 V (- 20...20 %) DC number of outputs4 relay discrete output number8 solid state 125 mA diagnostics function of moduleRelay output monitoring safety actuators Complementary power dissipation in W<= 3 W integrated connection typeBackplane expansion bus switching voltage10 V DC associated fuse rating3.5 A slow-blow safety levelSILCL 3 conforming to IEC 62061Can reach category 4 conforming to EN/ISO 13849-1Can reach PL = e conforming to EN/ISO 13849-1Can reach SIL 3 conforming to EN/IEC 61508 quality labelsCE output typeRelay, with 4 NO, volt-free quantity per set1 switching time12 ms maximum switching voltage250 V DC400 V AC minimum switching current20 mA maximum switching current6 A number of terminal blocks4 local signalling1 LED green with PWR marking for power ON1 LED green with RUN marking for RUN (status)1 LED red with E IN marking for internal error1 LED red with E EX marking for external error2 LEDs orange with ADDR marking for node address4 LEDs green/red with RELAY K1...K4 marking for relay contact4 LEDs yellow with RST marking for reset connections - terminals1-wire spring clamp terminals, removable terminal block2-wire spring clamp terminals, removable terminal block cable cross section(0.2...2.5 mm² - AWG 24...AWG 14) flexible cable without cable end(0.25...2.5 mm² - AWG 23...AWG 14) flexible cable with cable end, with bezel(0.2...2.5 mm² - AWG 24...AWG 14) solid cable without cable end(0.25...2.5 mm² - AWG 23...AWG 14) flexible cable with cable end, without bezel(0.5...1 mm² - AWG 20...AWG 18) flexible cable with cable end, with double bezel mounting supportOmega 35 mm DIN rail conforming to EN 50022 width22.5 mm height99 mm depth114.5 mm product weight0.3 kg Environment standardsEN/IEC 61508EN/IEC 61800-5-1EN/ISO 13849-1IEC 62061 product certificationscULusTÜVRCM IP degree of protectionIP20 ambient air temperature for operation-10...55 °C ambient air temperature for storage-20...85 °C relative humidity10...95 % pollution degree2 [Uimp] rated impulse withstand voltage4 kV conforming to EN/IEC 61800-5-1 safety reliability dataB10d = 300000 utilisation category AC-15 230 V, 3 A, conforming to EN/ISO 13849-1B10d = 750000 utilisation category AC-15 230 V, 1 A, conforming to EN/ISO 13849-1B10d = 10000000 utilisation category DC-13 24 V, 2 A, conforming to EN/ISO 13849-1 insulation250 V AC between power supply and housing conforming to EN/IEC 61800-5-1 overvoltage categoryII electromagnetic compatibilityElectrostatic discharge immunity test - test level 6 kV, on contact conforming to EN/IEC 61000-4-2Electrostatic discharge immunity test - test level 20 kV, on air conforming to EN/IEC 61000-4-2Susceptibility to electromagnetic fields - test level 10 V/m, 80...1000 MHz conforming to EN/IEC 61000-4-3Susceptibility to electromagnetic fields - test level 30 V/m, 1.4 GHz...2 GHz conforming to EN/IEC 61000-4-3 vibration resistance+/-0.35 mm (f = 10...55 Hz) conforming to EN/IEC 61496-1 shock resistance10 gn 1000 shocks on each axis 16 ms EN/IEC 61496-1 1000 shocks on each axis EN/IEC 61496-1 EN/IEC 61496-1 electrical durability20000000 cycles mechanical durability20000000 cycles service life20 yr Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profileAvailable Product end of life instructionsAvailable
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsCADSizeAdd to My DocumentsCAD files for XPSMCMRO0004G: XPSMCM Output expansion units. 4 relay outputs with cage clamp teminal. (Version 1.0)CertificateSizeAdd to My DocumentsInstruction sheetSizeAdd to My DocumentsDeclaration of conformitySizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.
Dimensions DrawingsDimensionsSpring Terminal
Mounting and ClearanceMounting Safety Controller CPU with Module(s)Mount BackPlane Connector on Rail1 :Connect as much Backplane Connector as module to be install.2 :Fix the connectors to the rail (Top first).Mount Safety Controller CPU with Other Module(s)1 :Mount controller CPU and modules on rail.2 :Make sure that the controller CPU or the module(s) are plugged on the BackPlane connector.
Connections and SchemaWiringCategory 2 Wiringa :Restartb :Feedbackc :Loadd :FuseCategory 4 Wiringa :Restartb :Feedbackc :Loadd :Fuse