Main range of productPreventa Safety automation product or component typeSafe speed monitoring module device short nameXPSMCM electrical connectionScrew terminal [Us] rated supply voltage24 V (- 20...20 %) DC discrete input voltage24 V DC function of moduleSpeed monitoring Complementary power consumption in W<= 3 W power dissipation in W3 W integrated connection typeBackplane expansion bus safety levelSILCL 3 conforming to IEC 62061Can reach category 4 conforming to EN/ISO 13849-1Can reach PL = e conforming to EN/ISO 13849-1Type 4 conforming to EN/IEC 61496-1 quality labelsCE number of terminal blocks4 local signalling1 LED green with PWR marking for power ON1 LED green with RUN marking for RUN (status)1 LED red with E IN marking for internal error1 LED red with E EX marking for external error2 LEDs orange with ADDR marking for node address1 LED yellow with ENC marking for encoder connection status2 LEDs yellow with PROX marking for proximity sensors connection status2 LEDs yellow with SH marking for speed monitoring status connections - terminals2-wire captive screw clamp terminals, removable terminal block1-wire captive screw clamp terminals, removable terminal block input frequency<= 5 kHz for sensor<= 500 kHz for encoder TTL sensor typeInductive proximity sensor electrical connection1 connector RJ45 conforming to EIA/TIA-568-A cable cross section(0.2...1.5 mm² - AWG 24...AWG 16) flexible cable without cable end(0.2...2.5 mm² - AWG 24...AWG 14) flexible cable without cable end(0.25...1 mm² - AWG 23...AWG 18) flexible cable with cable end, without bezel(0.25...2.5 mm² - AWG 23...AWG 14) flexible cable with cable end, with bezel(0.5...1.5 mm² - AWG 20...AWG 16) flexible cable with cable end, with double bezel(0.2...1 mm² - AWG 24...AWG 18) solid cable without cable end(0.2...2.5 mm² - AWG 24...AWG 14) solid cable without cable end(0.25...2.5 mm² - AWG 23...AWG 14) flexible cable with cable end, without bezel mounting supportOmega 35 mm DIN rail conforming to EN 50022 depth22.5 mm height99 mm width114.5 mm product weight0.28 kg Environment standardsEN/IEC 61496-1EN/IEC 61508EN/IEC 61800-5-1EN/ISO 13849-1IEC 62061 product certificationscULusTÜVRCM IP degree of protectionIP20 for enclosure ambient air temperature for operation-10...55 °C ambient air temperature for storage-20...85 °C relative humidity10...95 % pollution degree2 [Uimp] rated impulse withstand voltage4 kV conforming to EN/IEC 61800-5 insulation250 V AC between power supply and housing conforming to EN/IEC 61800-5-1 overvoltage categoryII electromagnetic compatibilityElectrostatic discharge immunity test - test level 6 kV, on contact conforming to EN/IEC 61000-4-2Electrostatic discharge immunity test - test level 20 kV, on air conforming to EN/IEC 61000-4-2Susceptibility to electromagnetic fields - test level 10 V/m, 80...1000 MHz conforming to EN/IEC 61000-4-3Susceptibility to electromagnetic fields - test level 30 V/m, 1.4 GHz...2 GHz conforming to EN/IEC 61000-4-3 vibration resistance+/-0.35 mm (f = 10...55 Hz) conforming to EN/IEC 61496-1 shock resistance10 gn (duration = 16 ms) shocks : 1000 shocks on each axis EN/IEC 61496-1 service life20 yr Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profileAvailable Product end of life instructionsAvailable
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsCADSizeAdd to My DocumentsCAD files for XPSMCMEN0100TT: XPSMCM Expansion module for safety speed monitoring 1 TTL input with screw terminal. (Version 1.0)CertificateSizeAdd to My DocumentsInstruction sheetSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.
Dimensions DrawingsDimensionsScrew Terminal
Mounting and ClearanceMounting Safety Controller CPU with Module(s)Mount BackPlane Connector on Rail1 :Connect as much Backplane Connector as module to be install.2 :Fix the connectors to the rail (Top first).Mount Safety Controller CPU with Other Module(s)1 :Mount controller CPU and modules on rail.2 :Make sure that the controller CPU or the module(s) are plugged on the BackPlane connector.
Connections and SchemaWiringTerminal Designation
24 VDC power supply
0 Vdc power supply
PROXIMITY 1 connections
PROXIMITY 2 connections