Preventa XPS MP, XPS MC, XPS MCM - XPSMCMCO0000S1G
Modular safety controllers
RS485 Safe communications expansion module 1 way with spring termShow more characteristics >
Main range of productPreventa Safety automation product or component typeSafe communication expansion module device short nameXPSMCM [Us] rated supply voltage24 V (- 20...20 %) DC Complementary power dissipation in W3 W safety levelCan reach category 4 conforming to EN/ISO 13849-1Can reach PL = e conforming to EN/ISO 13849-1Can reach SILCL 3 conforming to IEC 62061Can reach SIL 3 conforming to EN/IEC 61508 quality labelsCE range compatibilityPreventa XPSMCM connector type4 ways RS485 number of port1 communication port protocolRS485 current consumption0.125 mA cable distance between devices50 m local signallingGreen LED with ON marking for power ONGreen LED with RUN marking for operatingRed LED with E IN marking for internal errorRed LED with E EX marking for external error number of terminals2 connections - terminals1-wire spring clamp terminals, removable terminal block2-wire spring clamp terminals, removable terminal block cable cross section(0.2...2.5 mm² - AWG 24...AWG 14) flexible cable without cable end(0.25...2.5 mm² - AWG 23...AWG 14) flexible cable with cable end, with bezel(0.2...2.5 mm² - AWG 24...AWG 14) solid cable without cable end(0.25...2.5 mm² - AWG 23...AWG 14) flexible cable with cable end, without bezel(0.5...1 mm² - AWG 20...AWG 18) flexible cable with cable end, with double bezel mounting supportOmega 35 mm DIN rail conforming to EN 50022 width22.5 mm height99 mm depth114.5 mm product weight0.3 kg Environment product certificationscULusTÜVRCM IP degree of protectionIP20 ambient air temperature for operation-10...55 °C ambient air temperature for storage-20...85 °C relative humidity10...95 % pollution degree2 insulation250 V AC between power supply and housing conforming to EN/IEC 61800-5-1 overvoltage categoryII electromagnetic compatibilityElectrostatic discharge immunity test - test level 6 kV, on contact conforming to EN/IEC 61000-4-2Electrostatic discharge immunity test - test level 20 kV, on air conforming to EN/IEC 61000-4-2Susceptibility to electromagnetic fields - test level 10 V/m, 80...1000 MHz conforming to EN/IEC 61000-4-3Susceptibility to electromagnetic fields - test level 30 V/m, 1.4 GHz...2 GHz conforming to EN/IEC 61000-4-3 vibration resistance+/-0.35 mm (f = 10...55 Hz) conforming to EN/IEC 61496-1 shock resistance10 gn (duration = 16 ms) shocks : 1000 shocks on each axis EN/IEC 61496-1 operating altitude2000 m service life20 yr Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profileAvailable Product end of life instructionsAvailable
Documents and DownloadsLanguage
Instruction sheetSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.
Dimensions DrawingsDimensionsSpring Terminal
Mounting and ClearanceMounting Safety Controller CPU with Module(s)Mount BackPlane Connector on Rail1 :Connect as much Backplane Connector as module to be install.2 :Fix the connectors to the rail (Top first).Mount Safety Controller CPU with Other Module(s)1 :Mount controller CPU and modules on rail.2 :Make sure that the controller CPU or the module(s) are plugged on the BackPlane connector.
Connections and SchemaWiringTerminal Designation