RS485 Safe communications expansion module 1 way with screw termShow more characteristics >
Main range of productPreventa Safety automation product or component typeSafe communication expansion module device short nameXPSMCM [Us] rated supply voltage24 V (- 20...20 %) DC Complementary power dissipation in W3 W safety levelCan reach category 4 conforming to EN/ISO 13849-1Can reach PL = e conforming to EN/ISO 13849-1Can reach SILCL 3 conforming to IEC 62061Can reach SIL 3 conforming to EN/IEC 61508 quality labelsCE range compatibilityPreventa XPSMCM connector type4 ways RS485 number of port1 communication port protocolRS485 current consumption0.125 mA cable distance between devices50 m local signallingGreen LED with ON marking for power ONGreen LED with RUN marking for operatingRed LED with E IN marking for internal errorRed LED with E EX marking for external error number of terminals2 connections - terminals2-wire captive screw clamp terminals, removable terminal block1-wire captive screw clamp terminals, removable terminal block cable cross section(0.2...1.5 mm² - AWG 24...AWG 16) flexible cable without cable end(0.2...2.5 mm² - AWG 24...AWG 14) flexible cable without cable end(0.25...1 mm² - AWG 23...AWG 18) flexible cable with cable end, without bezel(0.25...2.5 mm² - AWG 23...AWG 14) flexible cable with cable end, with bezel(0.5...1.5 mm² - AWG 20...AWG 16) flexible cable with cable end, with double bezel(0.2...1 mm² - AWG 24...AWG 18) solid cable without cable end(0.2...2.5 mm² - AWG 24...AWG 14) solid cable without cable end(0.25...2.5 mm² - AWG 23...AWG 14) flexible cable with cable end, without bezel mounting supportOmega 35 mm DIN rail conforming to EN 50022 width22.5 mm height99 mm depth114.5 mm product weight0.3 kg Environment product certificationscULusRCMTÜV IP degree of protectionIP20 ambient air temperature for operation-10...55 °C ambient air temperature for storage-20...85 °C relative humidity10...95 % pollution degree2 insulation250 V AC between power supply and housing conforming to EN/IEC 61800-5-1 overvoltage categoryII electromagnetic compatibilityElectrostatic discharge immunity test - test level 6 kV, on contact conforming to EN/IEC 61000-4-2Electrostatic discharge immunity test - test level 20 kV, on air conforming to EN/IEC 61000-4-2Susceptibility to electromagnetic fields - test level 10 V/m, 80...1000 MHz conforming to EN/IEC 61000-4-3Susceptibility to electromagnetic fields - test level 30 V/m, 1.4 GHz...2 GHz conforming to EN/IEC 61000-4-3 vibration resistance+/-0.35 mm (f = 10...55 Hz) conforming to EN/IEC 61496-1 shock resistance10 gn (duration = 16 ms) shocks : 1000 shocks on each axis EN/IEC 61496-1 operating altitude2000 m service life20 yr Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW)Compliant - since 1450 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
REACh Product environmental profileAvailable Product end of life instructionsAvailable
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsUser guideSizeAdd to My DocumentsCADSizeAdd to My DocumentsCAD file (on TraceParts) for XPSMCMCO0000S1: RS485 Safe communications expansion module 1 way with screw term (Version 2.0)CertificateSizeAdd to My DocumentsInstruction sheetSizeAdd to My DocumentsXPSMCM. Modules d’extension de bus de terrain, Fiche d’instructions (Version 01)XPSMCM. Módulos de ampliación de bus de campo, Hoja de instrucciones (Version 01)XPSMCM. Módulos de expansão de barramento de campo, Planilha de instruções (Version 01)Declaration of conformitySizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.
Dimensions DrawingsDimensionsScrew Terminal
Mounting and ClearanceMounting Safety Controller CPU with Module(s)Mount BackPlane Connector on Rail1 :Connect as much Backplane Connector as module to be install.2 :Fix the connectors to the rail (Top first).Mount Safety Controller CPU with Other Module(s)1 :Mount controller CPU and modules on rail.2 :Make sure that the controller CPU or the module(s) are plugged on the BackPlane connector.
Connections and SchemaWiringTerminal Designation