overtravel power limit switch - manual reset - 4P - 50/25 A - 2/3P schemeShow more characteristics >
Add to My Products Remove from My Products
The maximum number of products that can be compared is 4
Main range of productXR and XF product or component typeOvertravel limit switches device short nameXF9 electrical circuit typePower circuit product specific applicationSafety of hoisting equipment materialAluminium alloy (case) type of operatorManual latching, restricted by a padlockable device number of poles4 [Ie] rated operational currentAC-3, Ie = 25 A) 3-pole scheme, Ie = 50 A) 2-pole scheme Complementary resetManual reset switch actuationHorizontal approach maximum displacement angle75 ° contacts type and compositionWithout auxiliary contact block contact operationSnap action [Ithe] conventional enclosed thermal current40 A at -25...40 °C 3-pole scheme80 A at -25...40 °C 2-pole scheme [Ui] rated insulation voltage600 V conforming to CSA C22.2 No 14500 V conforming to IEC 158-1500 V conforming to IEC 947-4500 V conforming to VDE 0110 group C rated breaking capacity180 kA at 660 V 2-pole scheme conforming to IEC 158-1400 kA at 500 V 2-pole scheme conforming to IEC 158-1 cable cross section1 flexible cable 1...6 mm²1 flexible cable 1.5...10 mm² without cable end1 solid cable 1.5...6 mm² without cable end2 flexible cable 1...4 mm² with cable end2 flexible cable 1.5...6 mm² without cable end2 solid cable 1.5...6 mm² without cable end cable entry2 entries tapped for Pg 21 cable gland product weight2.2 kg Environment standardsIEC 158-1IEC 947-4VDE 0660IEC 947-1NF C 63-110 product certificationsCSA protective treatmentTC ambient air temperature for operation-25...70 °C ambient air temperature for storage-40...70 °C IP degree of protectionIP54 conforming to EN/IEC 60529 Offer Sustainability RoHS (date code: YYWW) Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CertificateSizeAdd to My DocumentsDeclaration of conformitySizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.