Main range of productHarmony XB7 product or component typePilot light device short nameXB7 mounting diameter22 mm sale per indivisible quantity10 shape of signaling unit headRound cap/operator or lens colourWhite light sourceLED bulb baseIntegral LED [Us] rated supply voltage120 V AC, 50/60 Hz device presentationMonolithic product Complementary height29 mm width29 mm depth54 mm terminals description ISO n°1(X1-X2)PL product weight0.02 kg device mountingFixing hole: Ø 22.5 mm (22.3 +0.4/0) conforming to EN/IEC 60947-5-1 fixing center>= 30 x 40 mm on support panel, metal, thickness: 1...6 mm>= 30 x 40 mm on support panel, plastic, thickness: 2...6 mm fixing modeFixing nut beneath head recommended torque: 2...2.4 N.m connections - terminalsFaston connectors (1 x 6.35 mm) conforming to EN/IEC 60947-1Faston connectors (2 x 2.8 mm) conforming to EN/IEC 60947-1 [Ui] rated insulation voltage250 V (degree of pollution: 3) conforming to EN/IEC 60947-1 [Uimp] rated impulse withstand voltage6 kV conforming to EN/IEC 60947-1 signalling typeSteady supply voltage limits100...132 V AC current consumption18...21 mA service life70000 h at rated voltage and 25 °C Environment protective treatmentTH ambient air temperature for storage-40...70 °C ambient air temperature for operation-25...70 °C overvoltage categoryClass II conforming to IEC 60536 IP degree of protectionIP20 (rear face) conforming to IEC 60529IP65 (front face) conforming to IEC 60529 NEMA degree of protectionNEMA 4 conforming to UL 50 ENEMA 12 conforming to UL 50 E standardsEN/IEC 60947-1EN/IEC 60947-5-1JIS C 4520UL 508CSA C22.2 No 14 vibration resistance5 gn (f = 2...500 Hz) conforming to IEC 60068-2-6 shock resistance50 gn (duration = 11 ms) for half sine wave acceleration conforming to IEC 60068-2-27 electromagnetic compatibilityDisturbing field emission, class B conforming to EN 55011 Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CertificateSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.