Main range of productAltivar product or component typeLine choke product compatibilityATV61HD90N4D - line choke - 1 per driveATV61WD90N4 - line choke - 1 per driveATV61WD90N4C - line choke - 1 per driveATV71HD75N4 - line choke - 1 per driveATV71WD75N4 - line choke - 1 per drive number of phasesThree phase range compatibilityAltivar 71Altivar 61 device applicationReduction of current harmonics value of inductance0.155 mH [In] rated current184 A saturation current370 A thermal losses220 W electrical connectionBare wires diameter: 9 mm Complementary power supply frequency50...60 Hz max current1.65 x nominal current (duration = 60 s) maximum voltage drop at rated load5 % electrical insulation classClass F minimum clearance distance5.5 mm IEC 60664 leakage distance11.5 mm conforming to IEC 60664 net weight31 kg width280 mm height330 mm depth210 mm Environment standardsEN 50178IEC 60076 (with HD398)VDE 0160 level 1 IP degree of protectionChoke: IP00Terminals: IP00 environmental characteristic3B1 conforming to IEC 721-3-33C2 conforming to IEC 721-3-33S1 conforming to IEC 721-3-3 pollution degree2 conforming to EN 50178 vibration resistance1 gn (f= 13…200 Hz) conforming to IEC 60068-2-61.5 mm peak to peak (f= 3…13 Hz) conforming to IEC 60068-2-6 shock resistance15 gn for 11 ms conforming to IEC 60068-2-27 relative humidity0…95 % ambient air temperature for operation45…55 °C (with current derating of 2 % per °C)0…45 °C (without current derating) ambient air temperature for storage-25…70 °C operating altitude1000...3000 m with current derating 1 % per 100 m Offer Sustainability EU RoHS DirectivePro-active compliance (Product out of EU RoHS legal scope)
EU RoHS Declaration
Toxic heavy metal freeYes Mercury freeYes RoHS exemption information China RoHS Regulation Contractual warranty Warranty18 months
CatalogueFormatSizeAdd to My DocumentsCADFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
- All Languages7
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.