TSXPSY1610M is replaced by:
Main range of productModicon Premium Automation platform product or component typePower supply module Complementary primary voltage24 V DC 19.2...30 V input current<= 1500 mA 24 V inrush current100 A 24 V I²t on activation12.5 A².s It on activation0.2 A.s protection typeInternal fuse 3.5 A 5 x 20 mm time-delayed primary circuitOverload protection secondary circuitOvervoltage protection secondary circuitShort-circuit protection secondary circuit total useful secondary power30 W secondary power15 W 24 V DC15 W 5 V DC current at secondary voltage0.6 A 24 V DC relay power supply3 A 5 V DC markingCE local signalling1 LED green presence of voltages (OK)1 LED red battery fault (BAT) module formatStandard product weight0.54 kg Environment immunity to microbreaks<= 1 ms dielectric strength2000 V primary/earth2000 V primary/secondary standards73/23/EEC89/336/EEC92/31/EEC93/68/EECCSA C22.2 No 142IEC 61131-2UL 508CSA C22.2 No 213 Class I Division 2 Group ACSA C22.2 No 213 Class I Division 2 Group BCSA C22.2 No 213 Class I Division 2 Group CCSA C22.2 No 213 Class I Division 2 Group D product certificationsABSBVDNVGLLRRINARMRS ambient air temperature for operation0...60 °C ambient air temperature for storage-25...70 °C relative humidity10...95 % without condensation for operation5...95 % without condensation for storage operating altitude0...2000 m protective treatmentTC IP degree of protectionIP20 pollution degree2 Offer Sustainability RoHS (date code: YYWW)Compliant - since 0842 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
REACh Product end of life instructionsNeed no specific recycling operations Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CertificateSizeAdd to My DocumentsInstruction sheetSizeAdd to My DocumentsDeclaration of conformitySizeAdd to My DocumentsMarine certificateSizeAdd to My DocumentsBV Marine Certificate PREMIUM PLCs (Version 1.0)
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.