Main rangeEcoStruxure Building Expert product nameSE7000 Series device short nameSE7305 product or component typeRoom controller device applicationLow voltage fan coil PIR coverWith cover sensor type10 kOhm T2 NTC thermistor with measurement accuracy: +/- 0.2 °F Complementary range compatibilityEcoStruxure Building Expert communication cardEcoStruxure Building Expert sensorEcoStruxure Building Expert temperature sensorEcoStruxure Building Expert relayEcoStruxure Building Expert sensor coverplate [Us] rated supply voltage10...30 V AC 50/60 Hz rated operational power in VA2 VA electrical insulation classClass II network frequency50 Hz60 Hz communication port protocolZigbee protocol information displayedTemperature : - 40...122 °F Control accuracyFor temperature : +/- 0.9 °F at 70 °F typically calibrated number of inputs1 dry contact input number of outputs2 universal output output typeAnalog maximum number of control steps3 Output rating0...10 V DC , <= 5 mA into >= 2 kOhm resistance temperature setting range40...90 °F (heating)0.9 °F (per step)54...100 °F (cooling) AWG gaugeAWG 22...AWG 18 connections - terminalsScrew terminal width3.42 in depth1.5 in height4.92 in product weight0.75 lb(US) Environment Setting rangeHumidification : 10...90 %Dehumidification : 15...95 % ambient air temperature for operation32...122 °F ambient air temperature for storage-22...122 °F relative humidity0...95 % non-condensing standardsICES-003CSA C22.2 No 24UL 873FCC part 15 subpart C product certificationsFCCC-Tick : AS/NZS CISPR 22UL listed file E27734 CCN XPAXUL listed file E27734 CCN XPAX7CE directives89/336/EEC - electromagnetic compatibility Offer Sustainability RoHS (date code: YYWW)Compliant - since 1106 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
REAChReference contains SVHC above the threshold - Go to CaP for more details
Go to CaP for more details
Documents and DownloadsLanguage
Declaration of conformitySizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.