Main Range of productOdace product or component typePush-button switch device presentationMechanism with plastic fixing frame switch applicationRoller blind for automatism switch additional informationMechanical and electrical interlock between up/down type of packingPaint cover quantity per setSet of 5 Complementary device mountingFlush switch functionDouble push-button number of rocker2 actuatorPush-button fixing modeBy screws colour tintAluminium rated current10 A - 250 V AC 50/60 Hz minimum load breaking capacity200 operations 1.25 In and 1.1 Un number of terminals3 screwless terminals shape of screw headPozidriv No 1 clamping connection capacity1 x 1.5...2 x 2.5 mm² stranded cable(s)1 x 1.5...2 x 2.5 mm² flexible cable(s)1 x 1.5...2 x 2.5 mm² rigid cable(s) wire stripping length12 mm materialCentre plate : thermoplastic ABS-UV stabilisedSupport frame : PBT (polybutylene terephthalate) GF30Casing : PC (polycarbonate) GF10 FR height71 mm width71 mm depth33.6 mm embedding depth18.75 mm product weight0.04 kg Environment ambient air temperature for storage-5...50 °C dielectric strength2000 V ambient air temperature for operation5...35 °C standards2006/95/EECEN 60669-1 IK degree of protectionIK04 IP degree of protectionIP21D environmental characteristicWindow-cleaning fluidAcetoneOilPetrolAlcoholBleachUV resistantLiquid soapAmmonia environmental health and issuesHalogen free Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW)Compliant - since 1101 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
REACh Product environmental profileAvailable Product end of life instructionsNeed no specific recycling operations Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsUser guideSizeAdd to My DocumentsCertificateSizeAdd to My DocumentsInstruction sheetSizeAdd to My DocumentsDeclaration of conformitySizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.