RM4JA31F is replaced by:
Main range of productZelio Control product or component typeIndustrial measurement and control relays relay typeCurrent measurement relay relay nameRM4J relay monitored parametersOvercurrent or undercurrent detection time delayAdjustable 0.05...30 s power consumption in VA3.3 VA AC measurement range0.3...30 mA current AC 50/60 Hz0.3...30 mA current DC10...100 mA current AC 50/60 Hz10...100 mA current DC100...1000 mA current AC 50/60 Hz100...1000 mA current DC contacts type and composition2 C/O Complementary maximum switching voltage440 V AC [Us] rated supply voltage110...130 V AC, 50/60 Hz +/- 5 % operating voltage tolerance0.85...1.1 Uc output contacts2 C/O measuring cycle<= 80 ms internal input resistance33 Ohm10 Ohm1 Ohm permissible continuous overload0.15 A1.5 A0.05 A permissible non repetitive overload5 A0.2 A0.5 A setting accuracy of the switching threshold+/-5 % switching threshold drift<= 0.06 % per degree centigrade depending permissible ambient air temperature<= 0.5 % within the supply voltage range (0.85...1.1 Un) setting accuracy of time delay10 P time delay drift<= 0.07 % per degree centigrade depending on temperature<= 0.5 % within the supply voltage range (0.85...1.1 Un) hysteresis5...30 % adjustable of current threshold setting markingCE : EMC 89/336/EECCE : LVD 73/23/EEC overvoltage categoryIII conforming to IEC 60664-1 [Ui] rated insulation voltage500 V conforming to IEC supply disconnection value> 0.1 Uc operating positionAny position without derating connections - terminalsScrew terminals 2 x 1.5 mm², flexible cable with cable endScrew terminals 2 x 2.5 mm², flexible cable without cable end tightening torque0.6...1.1 N.m mechanical durability30000000 cycles [Ith] conventional free air thermal current8 A [Ie] rated operational current2 A at 24 V DC-13 70 °C conforming to IEC 60947-5-1/19912 A at 24 V DC-13 70 °C conforming to VDE 06603 A at 115 V AC-15 70 °C conforming to IEC 60947-5-1/19913 A at 115 V AC-15 70 °C conforming to VDE 06603 A at 24 V AC-15 70 °C conforming to IEC 60947-5-1/19913 A at 24 V AC-15 70 °C conforming to VDE 06603 A at 250 V AC-15 70 °C conforming to IEC 60947-5-1/19913 A at 250 V AC-15 70 °C conforming to VDE 06600.1 A at 250 V DC-13 70 °C conforming to IEC 60947-5-1/19910.1 A at 250 V DC-13 70 °C conforming to VDE 06600.3 A at 115 V DC-13 70 °C conforming to IEC 60947-5-1/19910.3 A at 115 V DC-13 70 °C conforming to VDE 0660 switching capacity in mA10 mA at 12 V switching voltage250 V AC contacts material90/10 silver nickel contacts number of cables2 width23 mm height78 mm depth80 mm terminals description ISO n°1(15-16-18)OC(C-B1-B2-B3)CO(A1-A2)CO(25-26-28)OC output relay stateTripped if A measured > A setTripped if V measured > V set 9 mm pitches2.5 product weight0.172 kg Environment electromagnetic compatibilityElectrostatic discharge - test level 6 kV, level 3 - contact discharge conforming to IEC 61000-4-2Electrostatic discharge - test level 8 kV, level 3 - air discharge conforming to IEC 61000-4-2 standardsEN/IEC 60255-6 product certificationsCSAULGL ambient air temperature for storage-40...85 °C ambient air temperature for operation-20...65 °C environmental characteristic3K3 relative humidity15...85 % conforming to IEC 60721-3-3 shock resistance15 gn for 11 ms conforming to IEC 60255-21-1 IP degree of protectionIP20 (terminals) conforming to IEC 60529IP50 (casing) conforming to IEC 60529 pollution degree3 conforming to IEC 60664-1 dielectric test voltage2.5 kV non-dissipating shock wave4.8 kV resistance to electrostatic discharge6 kV contact conforming to IEC 61000-4-2 level 38 kV air conforming to IEC 61000-4-2 level 3 resistance to electromagnetic fields10 V/m conforming to IEC 61000-4-3 level 3 resistance to fast transients2 kV conforming to IEC 61000-4-4 level 3 protection against electric shocks2 kV : level 3 conforming to IEC 61000-4-5 disturbance radiated/conductedCISPR 11 group 1 - class ACISPR 22 - class A Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
End of Life InformationSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.