plug-in relay - Zelio RHN - instantaneous - 4 C/O - 60 V DC - 5 AShow more characteristics >
Add to My Products Remove from My Products
The maximum number of products that can be compared is 4
Main range of productZelio Relay product or component typePlug-in relay device short nameRHN contacts type and composition4 C/O contact operationStandardInstantaneous [Uc] control circuit voltage60 V DC [Ithe] conventional enclosed thermal current5 A at <= 40 °C status LEDWithout control typeManual control coil interference suppressionWithout Complementary [Ui] rated insulation voltage250 V test levelsLevel A group mounting operating positionAny position minimum switching capacity150 mVA / 1 V150 mVA at 10 mA contact bounce time<= 10 ms voltage drop<= 100 V for 3 A at 24 V average resistance30 mOhm at 20 °C average coil consumption1.6 W at 20 °C control circuit voltage limits0.8...1.1 Uc conforming to IEC 60255 drop-out voltage threshold0.1...0.3 Uc time constant12 ms for open contact(s)15 ms for closed contact(s) mechanical durability20000000 cycles operating rate<= 6 cyc/mn operating time1...4 ms for energisation/de-energisation1.2...4 ms for de-energisation/energisation10...20 ms between energisation of coil and closing of NO contact at 20 °C2...7 ms between de-energisation of coil and closing of NC contact at 20 °C CAD overall width33 mm CAD overall height43 mm CAD overall depth54 mm terminals description ISO n°1(41-42-44)OC(A1-A2)CO(31-32-34)OC(21-22-24)OC(11-12-14)OC product weight0.09 kg Environment standardsVDE 0435BS 4794NF C 45-250IEC 60255 product certificationsEDFCSABVURUSSRASE protective treatmentTC dielectric strength2500 V ambient air temperature for operation-5...40 °C conforming to IEC 60255 ambient air temperature for storage-40...70 °C vibration resistance6 gn (f = 10...55 Hz) conforming to IEC 60068-2-66 gn (f = 10...55 Hz) conforming to NF C 20-616 shock resistance50 gn for 11 ms conforming to NF C 20-608 Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.