Main RangeSpacial ProductSpacial SFHD Specific applicationOutdoor heavy duty CertificationUL conforming to UL 508 A (2007)Bureau Veritas conforming to IEC 61969-3 (2011)Bureau Veritas conforming to IEC 61439-5 (2010)DEKRA conforming to IEC 62208 (2011)Bureau Veritas conforming to ISO 12944 (2007) device applicationMulti-purpose product or component typeSuitable enclosure Enclosure height with canopy1262 mm Canopy height62 mm enclosure nominal width600 mm Enclosure depth with canopy430 mm Enclosure depth400 mm installation accessory typeFloor-standing Available functions with accessoriesFloor managementSuitable for electronic 19" rackCouplingRoof management device composition1 locking system with handle and padlock2 sliding rails mounting plate1 mechanical retainer door1 plastic document pocket A4 format1 aluminium cable gland plate1 canopy1 door1 roof1 structure4 mounting plate bracket Complementary structure typeFormed from a single sectionPerforated structure with a pitch of 25 mmVertical uprights screwed with top and bottom framesPanels and doors built into the structure door typePlain number of doors1 door opening sideReversible 120 ° lock type4 points lock, handle with 1242E key lock and padlock on front door mounting plate descriptionWithout mounting plate Cable gland plate typePlain aluminium accessibility for operationFrontRearSides of enclosureBottomTop Maximum lifting load1000 kg removable partsMounting plate bracket fixed by by screwsSliding rail fixed by by screwsRear panel fixed by by screws for external partRoof fixed by by screwsCanopy fixed by by screws and clawsDoor fixed by by removable axis for hingeCable gland plate fixed by fixing nut materialSteel with anti-corrosive coating for frameZamak for hinge Surface finished paintedPolyester powder on enclosure colourEnclosure : grey RAL 7035Handle : grey RAL 7035 Specific order possible for special colourYes Environment standardsIEC 62208IEC 61969-3IEC 61439-5UL 508 A IP degree of protectionIP55 conforming to IEC 60529 IK degree of protectionIK10 conforming to IEC 62262 climatic withstandC4H level : conforming to ISO 12944 salt mist 720 h ambient air temperature for operation-45...80 °C conforming to IEC 61969-3 class 1 corrosion withstandC4H conforming to ISO 12944 Environmental withstandSolar radiation : class 1 up to 1120 W/m² conforming to IEC 61969-3 (2011)Surrounding air withstand : class 1 up to 180 km/h conforming to IEC 61969-3 (2011)Ultraviolet degradation test : class 1 conforming to ISO 4892-2 (2013)Formation of ice and frost : class 1 conforming to IEC 61969-3 (2011)Fauna and flora withstand : class 1 conforming to IEC 61969-3 (2011)Chemical substance : class 1 conforming to IEC 61969-3 (2011) Thermal managementWith external cooling Potential heat dissipation : 4000 WNatural : Potential heat dissipation : 480 W at 20 °CNatural : Potential heat dissipation : 480 W at 40 °CFan : Potential heat dissipation : 1500 W for a maximum noise level of 60 dBAccording to cooling architecture Potential heat dissipation : 1500 W Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW)Compliant - since 0940 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
REACh Product environmental profileAvailable Product end of life instructionsNeed no specific recycling operations
CatalogueSizeAdd to My DocumentsCatálogo de envolventes para exterior Heavy Duty - Envolventes concebidos para los entornos más exigentes (Version 1.1)Quick Selection Guide 2018 - Universal Enclosures - S3D version (Version 1.0)Quick Selection Guide 2018 - Universal Enclosures - CRN version (Version 1.0)Outdoor Heavy Duty enclosures catalogue - Toughest outdoor environments get their dedicated enclosures (Version 2.1)CADSizeAdd to My DocumentsCAD file (on TraceParts) for NSYSFHD12640: Spacial SFHD outdoor heavy duty - suitable enclosure - H1262 W600 D430 - IP55 (Version 2.0)CertificateSizeAdd to My DocumentsInstruction sheetSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.