Main rangeClimaSys product nameClimaSys CV product or component typeFan range compatibilitySpacialPrisma PPrisma G Type of filterG2 Flow rateFree flow rate with standard filter: 562 m3/h at 50 HzFree flow rate with standard filter: 586 m3/h at 60 Hz [Us] rated supply voltage207...244 V input voltage230 V 50/60 Hz CertificationCEEACREACHRoHSEMC directive 89/336 EEC additional information1 line of 10 characters maximum Complementary Absorbed power68 W 50 Hz85 W 60 Hz [In] rated current0.52 A 50 Hz0.87 A 60 Hz Noise level < at59 dB bearing typeBall height336 mm external: width316 mm external: depth161 mm external: cut-out dimensions291 x 291 mm net weight3.480 kg materialOutlet grille: injected thermoplastic (PC)Motor support: injected thermoplastic (ASA PC) colourOutlet grille: smoked black (RAL 9005)Motor support: black (RAL 9005) ambient air temperature for operation-15…60 °C ambient air temperature for storage-40…70 °C maximum pressure140 Pa flow rate 0 m³/h connections - terminalsTerminal block IP degree of protectionIP54 device composition1 axial motor1 external protective transparent smoked grille: front1 smart filter with dust sensor1 fan sensor ready to be mounted: rear of outlet grille1 cable gland1 cut-out template condition of useFilter must be cleaned and replaced regularlyFlow rates depends on the work point, see ProClima softwareOverfrequent filter replacement should be avoidedSurrounding environment must be relatively cleanOutside temperature must be 5 °C lower than inside temperature Offer Sustainability REACh Regulation REACh free of SVHCYes EU RoHS DirectiveUnder investigation Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins
CADSizeAdd to My DocumentsBrochureSizeAdd to My DocumentsInstruction sheetSizeAdd to My DocumentsCatalogue pageSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.