Main rangeClimaSys product nameCU product or component typeCooling unit mounting typeRoof of enclosure type of installationIndoor product destinationFor enclosure mounting modeBy screws input voltage230 V 50/60 Hz network number of phases1 phase cooling power240 W 50/60 Hz L35-L50410 W 50/60 Hz L35-L35 Complementary height264 mm width486 mm depth259 mm [In] rated current1.5 A inrush current4 A power consumption in W230 W at 50/60 Hz, L35-L35290 W at 50/60 Hz, L35-L50 energy efficiency ratio1.8 control typeElectronic controller temperature setting range20...55 °C at 50 Hz20...50 °C at 60 Hz ambient air temperature for operation20...46 °C, inside the enclosure55 °C, maximum20...55 °C at 50 Hz, outside the enclosure20...50 °C at 60 Hz, outside the enclosure Noise level65 dB conforming to EN/ISO 3746 pressure28 bar Flow rateInternal circuit : 235 m3/h at 50/60 HzExternal circuit : 330 m3/h at 50/60 Hz product weight18 kg cooling gas typeR134a (0.17 kg) Type of filterOptional external circuit filter protection typeThermal protection : T 4 AShort-circuit protection (magnetic) : materialSteel colourGrey RAL 7035 Environment product certificationsCE directives2004/108/EC - electromagnetic compatibility2006/42/EC - machinery2006/95/EC - low voltage directive standardsEN 60335-1EN 60204-1EN 378EN 60335-2-40EN/ISO 12100 IP degree of protectionIP54 on the internal circuit conforming to IEC 60529IP34 on the external circuit conforming to IEC 60529 Offer Sustainability RoHS (date code: YYWW)Compliant - since 0940 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsCADSizeAdd to My DocumentsCAD file (on TraceParts) for NSYCU400R: ClimaSys standard cooling unit roof of enclosure - 410W at 230 V (Version 2.0)Instruction sheetSizeAdd to My DocumentsEnd of Life InformationSizeAdd to My DocumentsProduct Environmental ProfileSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.