Main rangeUnica aesthetic nameUnica Top - Unica Class product or component typeKey card switch device applicationControl device presentationMechanism with zamak fixing frame cover plate colour tintAluminium Complementary [Ue] rated operational voltage230 V +/- 10 % AC 50 Hz rated current10 A load type230 V AC incandescent lamp - 1470 W230 V AC halogen lamp - 1470 W230 V AC fan - 1470 W230 V AC convector - 1470 WLow voltage halogen lamp with ferromagnetic transformer - 1000 VALow voltage halogen lamp with electronic transformer - 1470 VAFluorescent tube ferromagnetic ballast - 1470 VACompact fluorescent lamp - 1470 WLED lamp - 1470 WContactor condition of useControl through appropriate relay actuatorCard 54 x 86 x 0.85 mm (maximum) number of modules2 modules fuse typeElectronic maximum number of switchings50000 operations pilot lightLocator lamp markingVertical insertion pictogram connections - terminalsSoldered connectors clamping connection capacity<= 1 x 2.5 mm² for flexible cable(s)<= 1 x 2.5 mm² for rigid cable(s) fixing modeScrewScrews materialMechanism cover : ASA + PCFixing frame : zamak embedding depth14 mm depthUnica Top cover frame : 35 mmUnica Class cover frame : 35 mm width70.9 mm height70.9 mm product weight0.0645 kg Environment IP degree of protectionIP20 IK degree of protectionIK01 ambient air temperature for operation5...30 °C ambient air temperature for storage-20...60 °C environmental characteristicAcetoneAlcoholAmmoniaBleachLiquid soapOilPetrolUV resistantWindow-cleaning fluid environmental health and issuesHalogen free product certificationsFR ME63 B02736 standardsEN 61058-1 Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW)Compliant - since 0622 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
REACh Product environmental profileAvailable
Product Environmental Profile
Product end of life instructionsNeed no specific recycling operations Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.