Main rangePowerLogic product or component typeMulti-circuit energy meter product namePowerLogic EM4000 device short nameEM4033 power monitoringBasic instrumentation energy managementSub billing and cost allocationBilling analysis device applicationSub billing power quality analysisCompliance monitoring type of measurementActive and reactive powerPositive active energyPositive reactive energyNegative active energyNegative reactive energyApparent energyCurrent per phase, rmsVoltage per phase, rmsPulse countApparent power [Us] rated supply voltage277 V AC at 60 Hz network frequency60 Hz Complementary sampling rate256 samples/cycle display typeBacklit LCD messages display capacity2 lines of 16 characters current transformer inputSolid core CT, 0.333 V x 24 (single pole)Solid core CT, 0.333 V x 12 (single phase)Solid core CT, 0.333 V x 8 (three phase)Split core CT, 0.333 V x 24 (single pole)Split core CT, 0.333 V x 12 (single phase)Split core CT, 0.333 V x 8 (three phase) measurement voltage80...480 V without PTs480...999000 V with external PTs measurement accuracy+/- 0.5 % of the measuring range number of inputs2 pulse communication port protocolModbus TCP/IPBACnet IPFTPHTTPSNTP communication port supportRS485Ethernet RJ45 communication of dataPositive active energyPositive reactive energyNegative active energyNegative reactive energyApparent energyVoltage Environment mounting modeWall mount device mountingWall mounted enclosure typeNEMA type 1 type of installationIndoor installationEnclosed outdoor relative humidity90 % at 40 °C pollution degree2 ambient air temperature for operation-40...70 °C ambient air temperature for storage-40...70 °C operating altitude<= 3000 m standardsEN 55022FCC part 15 class BICES-003IEC 6100-4-5CSA C22.2 No 61010-1CSA C22.2 No 61010-1-4ANSI/TIA-968-A : 2002 product certificationsUL width30.5 cm depth5.5 cm height33.5 cm product weight4 kg
Documents and DownloadsLanguage
CatalogueSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.