Main range of productINFD40 rangeFupact product nameFupact INF device short nameINFD40 product or component typeSwitch-disconnector-fuse device applicationProtection poles description3P protected poles description3f fuse typeDIN fuse sizeNH000 network typeDCAC network frequency50/60 Hz Complementary control typeWithout handle rotary handle mounting locationFront rotary handle mounting styleExtendedDirect mounting supportDIN rail, with specific accessoriesMounting plate [Ie] rated operational currentAC-22A: 40 A AC 50/60 Hz 220/240 VAC-22A: 40 A AC 50/60 Hz 380/415 VAC-22A: 40 A AC 50/60 Hz 440/480 VAC-22A: 40 A AC 50/60 Hz 500/525 VAC-22A: 40 A AC 50/60 Hz 660/690 VAC-23A: 40 A AC 50/60 Hz 220/240 VAC-23A: 40 A AC 50/60 Hz 380/415 VAC-23A: 40 A AC 50/60 Hz 440/480 VAC-23A: 40 A AC 50/60 Hz 500/525 VAC-23A: 40 A AC 50/60 Hz 660/690 VDC-22A: 40 A DC 125 V 2 poles in seriesDC-22A: 40 A DC 250 V 2 poles in seriesDC-23A: 40 A DC 500 V 4 poles in seriesDC-23A: 40 A DC 750 V 4 poles in series [Ith] conventional free air thermal current24 A ( 70 °C ) horizontal26 A ( 65 °C ) horizontal28 A ( 60 °C ) horizontal28 A ( 70 °C ) vertical30 A ( 55 °C ) horizontal30 A ( 65 °C ) vertical32 A ( 50 °C ) horizontal32 A ( 60 °C ) vertical34 A ( 55 °C ) vertical36 A ( 40 °C ) horizontal38 A ( 45 °C ) vertical40 A ( 40 °C ) vertical34 A ( 45 °C ) horizontal36 A ( 50 °C ) vertical38 A ( 35 °C ) horizontal40 A ( 40 °C ) power dissipation per fuse: 4.5 W [Ithe] conventional enclosed thermal current40 A at 40 °C, Power dissipation per fuse: 4.5 W (300 mm x 350 mm x 200 mm) maximum power11 kW at 220/240 V AC 50/60 Hz22 kW at 500/525 V AC 50/60 Hz30 kW at 660/690 V AC 50/60 Hz18.5 kW at 380/400 V AC 50/60 Hz18.5 kW at 415 V AC 50/60 Hz rated dutyUninterrupted intermittent duty classClass 120 - 60 % [Ui] rated insulation voltage1000 V AC 50/60 Hz1000 V DC [Uimp] rated impulse withstand voltage12 kV [Ue] rated operational voltage250 V DC690 V AC 50/60 Hz690 V AC 50/60 Hz AC-20690 V DC DC-20 [Im] rated making and breaking capacityIcm 105 kA at 690 V conforming to DIN (with fuse)Icm 176 kA at 415 V conforming to BS (with fuse)Icm 220 kA at 500 V conforming to DIN (with fuse)Icn 100 kA at 500 V conforming to DIN (with fuse)Icn 50 kA at 690 V conforming to DIN (with fuse)Icn 80 kA at 415 V conforming to BS (with fuse)Icm 6 kA at 690 V (without fuse)Icm 9 kA at 415 V (without fuse)Icm 7.5 kA at 500 V (without fuse) suitability for isolationYes contact position indicatorYes contact operationDouble-break Environment mechanical durability10000 cycles electrical durabilityAC-22A: 1500 cycles 500 V AC 50/60 HzAC-22A: 1500 cycles 690 V AC 50/60 HzAC-23A: 1500 cycles 500 V AC 50/60 HzAC-23A: 1500 cycles 690 V AC 50/60 Hz [Icw] rated short-time withstand current1 kA for 1 s0.18 kA for 30 s0.22 kA for 20 s0.57 kA for 3 s designHorizontal design connections terminalsScrew clamp terminals connections - terminalsScrew clamp terminals 40 A 2.5…25 mm² flexibleScrew clamp terminals 40 A 2.5…25 mm² rigid tightening torque2 N.m for terminal height97 mm width106 mm depth133 mm standardsEN/IEC 60269-4EN/IEC 60269-1EN/IEC 60947-3EN/IEC 60947-1EN/IEC 60947-5 product certificationsKEMA-KEUR IP degree of protectionIP20 conforming to IEC 60529IP65 conforming to IEC 60529 IK degree of protectionIK07 conforming to EN 50102IK10 conforming to EN 50102 pollution degree3 ambient air temperature for operation-25…70 °C ambient air temperature for storage-50…85 °C Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation REACh free of SVHCYes EU RoHS DirectiveCompliant
EU RoHS Declaration
Toxic heavy metal freeYes Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Pro-active China RoHS declaration (out of China RoHS legal scope)
Environmental Disclosure Circularity ProfileNo need of specific recycling operations Contractual warranty Warranty18 months
CertificateSizeAdd to My DocumentsInstruction sheetSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.