Main rangeCompact product nameCompact NSX DC product or component typeSwitch disconnector device short nameCompact NSX630NA DC PV poles description4P network typeDC [Ue] rated operational voltage1000 V DC conforming to IEC 60947-3 [Ie] rated operational currentDC-22A: 630 A DC 1000 V [Ui] rated insulation voltage1000 V DC conforming to IEC 60947-3 [Uimp] rated impulse withstand voltage8 kV conforming to IEC 60947-3 [Ith] conventional free air thermal current630 A at 65 °C [Icm] rated short-circuit making capacity20 kA switch-disconnector alone breaking capacity codeNA suitability for isolationYes conforming to IEC 60947-3 contact position indicatorYes visible breakNo utilisation categoryDC-22A pollution degree3 conforming to IEC 60947-3 Complementary control typeToggle mounting modeFixed upside connectionFront downside connectionFront [Icw] rated short-time withstand current20 kA during 1 s conforming to IEC 60947-3 mechanical durability10000 cycles conforming to IEC 60947-3 electrical durability1000 cycles 1000 V DC In conforming to IEC 60947-3 connection pitch70 mm height327 mm width280 mm depth182 mm net weight18 kg Environment standardsEN/IEC 60947UL 508 product certificationsEACCCC IP degree of protectionIP20 conforming to IEC 60529 IK degree of protectionIK07 conforming to EN 50102 electrical shock protection classClass II Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation EU RoHS DirectiveUnder investigation Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Environmental Disclosure Circularity Profile WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins
CADSizeAdd to My DocumentsCAD file (on TraceParts) for LV438969: switch disconnector Compact NSX630b NA DC PV - 630 A - 4P (Version 2.0)Instruction sheetSizeAdd to My DocumentsDeclaration of conformitySizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.