Main rangeCompact product nameCompact NSX DC product or component typeCircuit breaker device short nameCompact NSX160 DC PV device applicationDistribution poles description4P protected poles description4t network typeDC [In] rated current160 A ( 40 °C ) [Ui] rated insulation voltage1000 V DC IEC 60947-2 [Uimp] rated impulse withstand voltage8 kV conforming to IEC 60947-2 [Ue] rated operational voltage1000 V DC conforming to IEC 60947-2 breaking capacity10 kA Icu at 1000 V DC conforming to IEC 60947-2 suitability for isolationYes conforming to IEC 60947-2 utilisation categoryCategory A trip unit nameTM-D trip unit technologyThermal-magnetic trip unit protection functionsLI trip unit rating160 A ( 40 °C ) protection typeOverload protection (thermal) LShort-circuit protection (magnetic) I pollution degree3 conforming to IEC 60947-2 Complementary control typeToggle mounting modeFixed mounting supportBackplate upside connectionFront downside connectionFront mechanical durability10000 cycles electrical durability1500 cycles 1000 V DC In conforming to IEC 60947-2 connection pitch35 mm local signallingPositive contact indication long time pick-up adjustment type IrAdjustable long time pick-up adjustment range0.7...1 x In long time delay adjustment typeFixed [tsd] short-time delay adjustment range0...1250 s height161 mm width140 mm depth186 mm product weight2.6 kg Environment standardsEN/IEC 60947 product certificationsEACCCC IP degree of protectionIP40 conforming to IEC 60529 IK degree of protectionIK07 conforming to EN 50102 Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW)Compliant - since 0819 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
REACh Product environmental profileAvailable Product end of life instructionsAvailable Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CADSizeAdd to My DocumentsInstruction sheetSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.