Main rangeCompact product nameCompact NSX DC product or component typeSwitch disconnector device short nameCompact NSX630NA DC poles description3P network typeDC [Ie] rated operational currentDC-22A : 630 A DC 750 V [Ui] rated insulation voltage750 V DC conforming to IEC 60947-3 [Uimp] rated impulse withstand voltage8 kV conforming to IEC 60947-3 [Ith] conventional free air thermal current630 A [Icm] rated short-circuit making capacity7.5 kA switch-disconnector alone [Ue] rated operational voltage750 V DC conforming to IEC 60947-3 breaking capacity codeNA suitability for isolationYes conforming to EN 60947-3 contact position indicatorYes visible breakNo utilisation categoryDC-22A pollution degree3 conforming to IEC 60947-3 Complementary control typeToggle mounting modeFixed upside connectionFront downside connectionFront [Icw] rated short-time withstand current7.5 kA ( 1 s ) conforming to IEC 60947-3 mechanical durability5000 cycles conforming to IEC 60947-3 electrical durability1000 cycles 750 V DC In conforming to IEC 60947-32000 cycles 750 V DC In/2 connection pitch45 mm height255 mm width140 mm depth110 mm product weight6 kg Environment standardsEN/IEC 60947UL 508 product certificationsCCCEAC IP degree of protectionIP20 conforming to IEC 60529 electrical shock protection classClass II Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW)Compliant - since 1440 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
REACh Product environmental profileAvailable
Product Environmental Profile
Product end of life instructionsNeed no specific recycling operations
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsCADSizeAdd to My DocumentsSwitch-disconnector Compact NSX400/630 NA DC 3P (Version 1.0)CAD file (on TraceParts) for LV438154: switch-disconnector Compact NSX400...630NA DC - 630 A - 3P - fixed (Version 2.0)Instruction sheetSizeAdd to My DocumentsProduct Environmental ProfileSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.