Main rangeCompact product nameCompact NSX product or component typeCircuit breaker with Vigi add-on device short nameVigiCompact NSX100F device applicationDistribution poles description4P protected poles description4t neutral positionLeft network typeAC network frequency50/60 Hz [In] rated current100 A ( 40 °C ) [Ui] rated insulation voltage800 V AC 50/60 Hz [Uimp] rated impulse withstand voltage8 kV [Ue] rated operational voltage440 V AC 50/60 Hz breaking capacity codeF (36 kA) AC breaking capacity8 kA Icu at 660/690 V AC 50/60 Hz conforming to IEC 60947-222 kA Icu at 525 V AC 50/60 Hz conforming to IEC 60947-225 kA Icu at 500 V AC 50/60 Hz conforming to IEC 60947-235 kA Icu at 440 V AC 50/60 Hz conforming to IEC 60947-236 kA Icu at 380/415 V AC 50/60 Hz conforming to IEC 60947-285 kA Icu at 220/240 V AC 50/60 Hz conforming to IEC 60947-210 kA at 600 V AC 50/60 Hz conforming to UL 50825 kA at 480 V AC 50/60 Hz conforming to UL 50885 kA at 240 V AC 50/60 Hz conforming to UL 508 [Ics] rated service breaking capacityIcs 11 kA 525 V AC 50/60 Hz conforming to IEC 60947-2Ics 35 kA 440 V AC 50/60 Hz conforming to IEC 60947-2Ics 36 kA 380/415 V AC 50/60 Hz conforming to IEC 60947-2Ics 4 kA 660/690 V AC 50/60 Hz conforming to IEC 60947-2Ics 85 kA 220/240 V AC 50/60 Hz conforming to IEC 60947-2Ics 12.5 kA 500 V AC 50/60 Hz conforming to IEC 60947-2 suitability for isolationYes conforming to EN 60947-2Yes conforming to IEC 60947-2 utilisation categoryCategory A trip unit nameTM-D trip unit technologyThermal-magnetic trip unit protection functionsLI trip unit rating80 A ( 40 °C ) protection typeOverload protection (thermal) LShort-circuit protection (magnetic) I earth-leakage add-on module nameMH pollution degree3 conforming to IEC 60664-1 Complementary control typeToggle mounting modeFixed mounting supportBackplate upside connectionFront downside connectionFront mechanical durability50000 cycles electrical durability10000 cycles 690 V In conforming to IEC 60947-220000 cycles 690 V In/2 conforming to IEC 60947-230000 cycles 440 V In conforming to IEC 60947-250000 cycles 440 V In/2 conforming to IEC 60947-2 connection pitch35 mm local signallingPositive contact indication neutral protection setting1 x Ir 4t long time pick-up adjustment type IrAdjustable long time pick-up adjustment range0.7...1 x In long time delay adjustment typeFixed [tr] long-time delay adjustment range15 s 6 x Ir120...400 s 1.5 x In short-time pick-up adjustment type IsdFixed [Isd] short-time pick-up adjustment range640 A short-time delay adjustment typeFixed earth-leakage protection classClass A earth-leakage protectionWith residual earth-leakage sensitity adjustment typeAdjustable 5 settings [IΔn] residual earth-leakage sensitive adjustment0.03...10 A residual earth-leakage time delay adjustment typeAdjustable 4 settings height236 mm width140 mm depth86 mm product weight2.4 kg Environment overvoltage categoryClass II electrical shock protection classClass II standardsEN/IEC 60947UL 508 product certificationsEACMarineCCC IP degree of protectionIP40 conforming to IEC 60529 IK degree of protectionIK07 conforming to IEC 62262 ambient air temperature for operation-35...70 °C ambient air temperature for storage-55...85 °C Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW)Compliant - since 0839 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
REACh Product environmental profileAvailable Product end of life instructionsAvailable Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsUser guideSizeAdd to My DocumentsCADSizeAdd to My Documents4P3D VIGI MH NSX100F (Version 1.0)4P NSX100-250; VigiCompact circuit breaker (Version 1.0)NSX100/160/250 4P; VigiCompact circuit breaker4P NSX100-250; VigiCompact circuit breaker (Version 1.0)4P NSX100-250; VigiCompact circuit breaker (Version 1.0)Compact circuit breaker (Version 1.0)Instruction sheetSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.