Main range of productNSX100...250NSX100...250 DC product or component typeTrip unit range compatibilityCompact NSX100Compact NSX100 DC device applicationGenerator poles description4P protected poles description3t + 1.6 N3t + N/24t neutral positionLeft network typeACDC network frequency50/60 Hz trip unit nameTM-G trip unit technologyThermal-magnetic trip unit protection functionsLI trip unit rating16 A 40 °C protection typeOverload protection (thermal) LShort-circuit protection (magnetic) I Complementary mounting modeFixed [Ue] rated operational voltage690 V AC 50/60 Hz750 V DC neutral protection setting1 x Ir 4t1.6 x Ir 3t + OSNNo protection 3t long time pick-up adjustment type IrAdjustable [Ir] long time pick-up adjustment range0.7...1 x In long time delay adjustment typeFixed [tr] long-time delay adjustment range120...400 s at 1.5 x In short-time pick-up adjustment type IsdFixed [Isd] short-time pick-up adjustment range63 A short-time delay adjustment typeFixed communication of dataEnergy meteringInstantaneous and demand valuesMaintenance indicatorsMaximeters/minimetersPower qualityProtection and alarm settingsTime-stamped histories and event tables Environment standardsEN/IEC 60947-2UL 508 product certificationsCCCMarineEAC ambient air temperature for operation-25...70 °C ambient air temperature for storage-50...85 °C Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW)Compliant - since 0819 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
REACh Product environmental profileAvailable
Product Environmental Profile
Product end of life instructionsNeed no specific recycling operations Contractual warranty Warranty period18 months
CatalogueSizeAdd to My DocumentsUser guideSizeAdd to My DocumentsCADSizeAdd to My DocumentsCAD file (on TraceParts) for LV429165: trip unit - TMG - 16 A - 4 poles 4d (Version 2.0)Instruction sheetSizeAdd to My DocumentsProduct Environmental ProfileSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.