Main range of productNSX100...250 product or component typeControl unit range compatibilityCompact NSX100Compact NSX160Compact NSX250 device applicationGenerator poles description4P protected poles description3t3t + N/24t neutral positionLeft network typeAC network frequency50/60 Hz trip unit nameMicrologic 2.2 G trip unit technologyElectronic trip unit protection functionsLSoI trip unit rating40 A 40 °C protection typeOverload protection (long time) LShort time short-circuit protection with fixed delay SoInstantaneous short-circuit protection I Complementary mounting modeFixed [Ue] rated operational voltage690 V AC 50/60 Hz neutral protection setting0.5 x Ir 3t + N/21 x Ir 4tNo protection 3t long time pick-up adjustment type IrAdjustable 9 settings [Ir] long time pick-up adjustment range0.9...1 x Io long time delay adjustment typeFixed [tr] long-time delay adjustment range15 s at 1.5 x Ir0.35 s at 7.2 x Ir0.5 s at 6 x Ir thermal memory20 minutes before and after tripping short-time pick-up adjustment type IsdAdjustable [Isd] short-time pick-up adjustment range1.5...9 x Ir short-time delay adjustment typeFixed [tsd] short-time delay adjustment range0.14 s instantaneous pick-up adjustment type IiFixed [Ii] instantaneous pick-up adjustment range600 A Environment standardsEN/IEC 60947-2UL 508 product certificationsCCCMarineEAC ambient air temperature for operation-25...70 °C ambient air temperature for storage-50...85 °C Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW)Compliant - since 0819 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
REACh Product environmental profileAvailable Product end of life instructionsAvailable Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsUser guideSizeAdd to My DocumentsCADSizeAdd to My DocumentsCAD file (on TraceParts) for LV429086: trip unit - Micrologic 2.2 G - 40 A - 4 poles 4d (Version 2.0)Instruction sheetSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.