trip unit Micrologic 2.2 for Compact NSX 100/160/250 circuit breakers, electronic, rating 100A, 3 poles 3dShow more characteristics >
Add to My Products Remove from My Products
The maximum number of products that can be compared is 4
Main range of productNSX100...250 product or component typeControl unit range compatibilityCompact NSX100Compact NSX160Compact NSX250 device applicationDistribution poles description3P protected poles description3t network typeAC network frequency50/60 Hz trip unit nameMicrologic 2.2 trip unit technologyElectronic trip unit protection functionsLSoI trip unit rating100 A 40 °C protection typeOverload protection (long time) LShort time short-circuit protection with fixed delay SoInstantaneous short-circuit protection I Complementary mounting modeFixed [Ue] rated operational voltage690 V AC 50/60 Hz long time pick-up adjustment type IrAdjustable 9 settings [Ir] long time pick-up adjustment range0.9...1 x Io long time delay adjustment typeFixed [tr] long-time delay adjustment range11 s at 7.2 x Ir16 s at 6 x Ir400 s at 1.5 x Ir thermal memory20 minutes before and after tripping short-time pick-up adjustment type IsdAdjustable 9 settings [Isd] short-time pick-up adjustment range1.5...10 x Ir short-time delay adjustment typeFixed [tsd] short-time delay adjustment range0.02 s instantaneous pick-up adjustment type IiFixed [Ii] instantaneous pick-up adjustment range1500 A Environment standardsEN/IEC 60947-2UL 508 product certificationsCCCMarineEAC ambient air temperature for operation-25...70 °C ambient air temperature for storage-50...85 °C Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW)Compliant - since 0819 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
REACh Product environmental profileAvailable Product end of life instructionsAvailable Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.