trip unit TM40D, Compact NSX 100/160, thermal magnetic, distribution protection, 40 A rating, 4P 4dShow more characteristics >
Add to My Products Remove from My Products
The maximum number of products that can be compared is 4
Main range of productNSX100...250 DCNSX100...250 product or component typeTrip unit range compatibilityCompact NSX100Compact NSX160Compact NSX100 DC device applicationDistribution poles description4P protected poles description4t neutral positionLeft network typeDCAC network frequency50/60 Hz trip unit nameTM-D trip unit technologyThermal-magnetic trip unit protection functionsLI trip unit rating40 A 40 °C protection typeOverload protection (thermal) LShort-circuit protection (magnetic) I Complementary mounting modeFixed [Ue] rated operational voltage690 V AC 50/60 Hz750 V DC neutral protection setting1 x Ir 4t long time pick-up adjustment type IrAdjustable [Ir] long time pick-up adjustment range0.7...1 x In long time delay adjustment typeFixed [tr] long-time delay adjustment range120...400 s at 1.5 x In15 s at 6 x Ir short-time pick-up adjustment type IsdFixed [Isd] short-time pick-up adjustment range500 A short-time delay adjustment typeFixed Environment standardsUL 508EN/IEC 60947-2 product certificationsCCCEACMarine ambient air temperature for operation-25...70 °C ambient air temperature for storage-50...85 °C Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profile Product end of life instructionsNeed no specific recycling operations Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsUser guideSizeAdd to My DocumentsCADSizeAdd to My Documents4P3D TM TRIP UNIT FOR NSX100 CIRCUIT (Version 1.0)CAD files for LV429054: 4P3D TM TRIP UNIT FOR NSX100-250 CIRCUIT (Version 1.0)Instruction sheetSizeAdd to My DocumentsProduct Environmental ProfileSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.