circuit breaker Compact NSXm E (16 kA at 415 VAC), 3P, 100 A rating Micrologic Vigi 4.1 trip unit, compression lugs and busbar connectorsShow more characteristics >
Add to My Products Remove from My Products
The maximum number of products that can be compared is 4
Main rangeCompact product nameCompact NSXm Micrologic Vigi 4.1 device short nameNSXm 100E product or component typeEarth leakage circuit breaker device applicationDistributionProtection Complementary [In] rated current100 A poles description3P 3d neutral positionLeft control typeToggle mounting modeBy screws for plateClip-on for DIN rail network typeAC network frequency50/60 Hz breaking capacity codeE 16 kA 415 V AC [Icu] rated ultimate breaking capacity25 kA at 220...240 V AC 50/60 Hz according to IEC 60947-216 kA at 380...415 V AC 50/60 Hz according to IEC 60947-210 kA at 440 V AC 50/60 Hz according to IEC 60947-2 [Ue] rated operational voltage440 V AC 50/60 Hz according to IEC 60947-2 [Ics] rated service breaking capacity25 kA at 220...240 V AC 50/60 Hz according to IEC 60947-216 kA at 380...415 V AC 50/60 Hz according to IEC 60947-210 kA at 440 V AC 50/60 Hz according to IEC 60947-2 [Uimp] rated impulse withstand voltage8 kV according to IEC 60947-2 [Ui] rated insulation voltage500 V according to IEC 60947-2 trip unit technologyElectronic trip unit nameMicrologic 4.1 trip unit protection functionsLSoIR trip unit rating100 A at 40 °C protection typeOverload protection (long time)Short time short-circuit protectionInstantaneous short-circuit protectionEarth-leakage protection thermal memory20 minutes before and after tripping long time pick-up adjustment range0.4...1 x In [tr] long-time delay adjustment rangeAt 7.2 x Ir Tr= 5 sAt 6 x Ir Tr= 8 sAt 1.5 x Ir Tr= 200 s short-time pick-up adjustment type IsdAdjustable 9 settings [Isd] short-time pick-up adjustment range1.5...10 x Ir short-time delay adjustment typeFixed instantaneous pick-up range1500 A earth-leakage sensitivity30 mA for class A100 mA for class A300 mA for class A500 mA for class A1000 mA for class A30 mA for class AC100 mA for class AC300 mA for class AC500 mA for class AC1000 mA for class AC3000 mA for class AC5000 mA for class AC [IΔn] residual earth-leakage sensitive adjustment300 mA3 A500 mA30 mA5 A100 mA1 A [Δt] residual earth-leakage time delay adjustment0 ms60 ms150 ms1000 ms500 ms suitability for isolationYes according to IEC 60947-2 utilisation categoryCategory A 9 mm pitches9 module connection pitch35 mm with spreaders27 mm without spreaders connections - terminalsCompression lug/busbar thread typeM6 thicknessUp to 8 mm local signallingGreen flag for presence of auxiliary contacts number of slots1 slot(s) for auxiliary switch OF1 slot(s) for alarm switch SD1 slot(s) for voltage release MN or MX Power wire stripping length20 mm Environment quality labelsCE standardsEN/IEC 60947 product certificationsCCCEAC colourGrey (RAL 7016) IP degree of protectionIP40 (front cover) according to IEC 60529 IK degree of protectionIK07 according to IEC 62262 pollution degree3 according to IEC 60947-1 ambient air temperature for operation-25...70 °C ambient air temperature for storage-40...85 °C operating altitude5000 m with derating2000 m without derating Mechanical durability20000 cycles according to IEC 947-1 Annex K ed 5.2 for In Electrical durability10000 cycles according to IEC 947-1 Annex F ed 5.2 for In at 440 V height144 mm width108 mm depth80 mm product weight1.63 kg Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profile Product end of life instructions
Documents and DownloadsLanguage
User guideSizeAdd to My DocumentsCompact NSXm - Circuit Breakers, Earth-Leakage Circuit Breakers and Switch Disconnectors - User Guide (Version 01)CADSizeAdd to My DocumentsCAD files for LV426752: NSXm 16kA to 70kA Vigi 25A to 160A 3P busbar circuit breaker (Version 1.0)Instruction sheetSizeAdd to My DocumentsEnd of Life InformationSizeAdd to My DocumentsProduct Environmental ProfileSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.