Main rangeTeSys product nameTeSys LF device short nameLF4MP product or component typeEnclosed DOL reversing starter device applicationAS interface device compositionReversing contactorCircuit-breakerAS interface module utilisation categoryAC-3 network typeAC [Uc] control circuit voltage24 V for AC circuit at 50/60 Hz thermal protection adjustment range4...6.3 A control typeKey switch 2 positions for local/AS-Interface control - bus - localRotary handle for protection control - OFF - Trip - ONSelector switch 3 positions for start/stop/start - 1 - 0 - 2 Complementary motor power kW1.1 kW at 220/230 V - AC at 50/60 Hz2.2 kW at 400/415 V - AC at 50/60 Hz network frequency50/60 Hz [Ue] rated operational voltage415 V - AC at 50/60 Hz for power circuit250 V - AC at 50/60 Hz for output control relay30 V - DC for output control relay [Uimp] rated impulse withstand voltage6 kV for power circuit conforming to IEC 60947-12.5 kV for 24 V conforming to IEC 60947-12.5 kV for sensor conforming to IEC 60947-12.5 kV for AS-Interface conforming to IEC 60947-1 insulation resistance> 1000 mOhm between output and communication insulation1500 V between output and ground1500 V between output and internal logicBetween input and communication [Ui] rated insulation voltage415 V AC at 50/60 Hz conforming to IEC 60947 [Ithe] conventional enclosed thermal current5 A for output control relay at 40 °C protection typeInductive overvoltagePhase failureShort-circuit protection (magnetic)Thermal protection breaking capacity100 kA at 230/240 V conforming to IEC 60947-2100 kA at 400/415 V conforming to IEC 60947-2 mechanical durabilityCircuit breaker : 0.1 McyclesContactor : 30 Mcycles electrical durabilityCircuit breaker : 0.1 McyclesContactor : 0.8 Mcycles - AC-3 - 8.5 ARelay : 0.1 Mcycles - 24 V with 6 cyc/mn - AC-12 - 5 ARelay : 1 Mcycles - 24 V with 15 cyc/mn - AC-12 - 1 ARelay : 0.5 Mcycles - 24 V with 15 cyc/mn - AC-14 - 1 ARelay : 1 Mcycles - 24 V with 15 cyc/mn - AC-14 - 0.5 ARelay : 5 Mcycles - 24 V with 30 cyc/mn - AC-14 - 0.25 ARelay : 0.1 Mcycles - 24 V with 6 cyc/mn - DC-12 - 5 ARelay : 0.2 Mcycles - 24 V with 6 cyc/mn - DC-12 - 2 ARelay : 0.5 Mcycles - 24 V with 15 cyc/mn - DC-3 - 1 ARelay : >= 1 Mcycles - 24 V with 30 cyc/mn - DC-3 - 0.25 A current consumption20 mA for communication bus during operation60 mA for communication bus sensor0 mA at 24 V for supply circuit de-energisation30 mA at 24 V for supply circuit maintained mode110 mA at 24 V for supply circuit inrush20 mA for output relay local signallingProduct status by 3 LEDsInput/output status by LED number of inputs2 M12 nominal input value19...30 V 50 mA - DC input descriptionStatus D0 : forward stop - bit value 0Status D1 : reverse stop - bit value 0Status D2 : disable relay - bit value 0Status D3 : unused - bit value 0Status D0 : forward start - bit value 1Status D1 : reverse start - bit value 1Status D2 : enable relay - bit value 1Status D3 : unused - bit value 1 input typeResistive sensor compatibility2 or 3-wire PNP output descriptionCommand D0 : not ready - bit value 0Command D1 : stopped - bit value 0Command D2 : sensor 1 missing - bit value 0Command D3 : sensor 2 missing - bit value 0Command D0 : ready - bit value 1Command D1 : started - bit value 1Command D2 : sensor 1 present - bit value 1Command D3 : sensor 2 present - bit value 1 response timeOutput control relay : <= 10 ms during closingOutput control relay : <= 15 ms during opening contacts type and composition1 C/O AS-interface profile7DFF - standard connections - terminalsOutput control relay : HARTING socketSupply circuit : HARTING socketPower circuit : screw clamp terminals - flexible without cable endPower circuit : screw clamp terminals - flexible with cable endPower circuit : screw clamp terminals - rigid tightening torquePower circuit : 0.8 N.m - with screwdriver flat Ø 5.5 mm width279 mm height245 mm depth179 mm product weight1.6 kg Environment electromagnetic compatibilityElectrostatic discharge 8 kV level 3 - in air - conforming to EN/IEC 61000-4-2Electrostatic discharge 4 kV level 2 - in indirect mode - conforming to EN/IEC 61000-4-2Electrical fast transient/burst immunity test 2 kV level 3 conforming to EN/IEC 61000-4-4Surge immunity test 4 kV level 4 - power, line to ground - conforming to IEC 61000-4-5Surge immunity test 2 kV level 4 - power, line to line - conforming to EN/IEC 61000-4-5Surge immunity test 2 kV level 2 - control circuit, line to ground - conforming to IEC 61000-4-5Surge immunity test 500 V level 2 - control circuit, line to line - conforming to EN/IEC 61000-4-5Conducted RF disturbances 10 V/m conforming to IEC 61000-4-6Conducted RF disturbances 10 V/m conforming to ENV 50141Radiated radio-frequency electromagnetic field immunity test 10 V/m conforming to IEC 61000-4-3Radiated radio-frequency electromagnetic field immunity test 10 V/m conforming to ENV 50204Radiated radio-frequency electromagnetic field immunity test 10 V/m conforming to ENV 50140Disturbing field emission class B conforming to ENV 55011Disturbing field emission class B conforming to CISPR 11 mechanical robustnessShocks : 10 Gn during contactor open conforming to IEC 60068-2-27Shocks : 15 gn during contactor closed conforming to IEC 60068-2-27Vibrations : 2 Gn during contactor open conforming to IEC 60068-2-6Vibrations : 4 Gn during contactor closed conforming to IEC 60068-2-6 IP degree of protectionIP54 conforming to IEC 60529 protective treatmentTC fire resistance960 °C conforming to IEC 60695-2-1 operating altitude2000 m standardsEN 60204-1EN 60439-1EN 60947-1IEC 60204-1IEC 60439-1IEC 60947-1 materialSteel - white : RAL 9001 ambient air temperature for operation-5...40 °C conforming to IEC 61439-1 ambient air temperature for storage-40...80 °C conforming to IEC 61439-1 Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profile Product end of life instructions
Documents and DownloadsLanguage
End of Life InformationSizeAdd to My DocumentsProduct Environmental ProfileSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.