View all TeSys F
TeSys F contactor - 4P (4 NO) - AC-1 - <= 440 V 1600 A - coil 125 V DCShow more characteristics
LC1F7804GD has not been replaced. Please contact your customer care center for more information.
Add to My Products Remove from My Products
The maximum number of products that can be compared is 4
Main rangeTeSys product nameTeSys F product or component typeContactor device short nameLC1F contactor applicationResistive load utilisation categoryAC-1 poles description4P power pole contact composition4 NO [Ue] rated operational voltage<= 1000 V AC 50/60 Hz<= 460 V DC [Ie] rated operational current1600 A (at <40 °C) at <= 440 V AC AC-1 [Uc] control circuit voltage125 V DC coil typeStandard Complementary [Uimp] rated impulse withstand voltage8 kV overvoltage categoryIII [Ith] conventional free air thermal current1600 A (at 40 °C) rated breaking capacity6240 A conforming to IEC 60947-4-1 [Icw] rated short-time withstand current3000 A 40 °C - 3 min6250 A 40 °C - 10 s5600 A 40 °C - 30 s4600 A 40 °C - 1 min2200 A 40 °C - 10 min associated fuse rating1600 A gG at <= 440 V800 A aM at <= 440 V average impedance0.1 mOhm - Ith 1600 A 50 Hz [Ui] rated insulation voltage1000 V conforming to IEC 60947-4-11500 V conforming to VDE 0110 group C power dissipation per pole250 W AC-1 mounting supportPlate standardsIEC 60947-1EN 60947-4-1EN 60947-1JIS C8201-4-1IEC 60947-4-1 product certificationsBVRINAABSDNVULCBLROS (Lloyds register of shipping)RMRoSCCC connections - terminalsControl circuit: screw clamp terminals 1 cable(s) 1…4 mm²flexible without cable endControl circuit: screw clamp terminals 2 cable(s) 1…4 mm²flexible without cable endControl circuit: screw clamp terminals 1 cable(s) 1…4 mm²flexible with cable endControl circuit: screw clamp terminals 2 cable(s) 1…2.5 mm²flexible with cable endControl circuit: screw clamp terminals 1 cable(s) 1…4 mm²solid without cable endControl circuit: screw clamp terminals 2 cable(s) 1…4 mm²solid without cable endPower circuit: bar 2 cable(s) - busbar cross section: 100 x 5 mmPower circuit: bolted connection tightening torqueControl circuit: 1.2 N.mPower circuit: 58 N.m control circuit voltage limitsOperational: 0.85...1.1 Uc (at 55 °C)Drop-out: 0.2...0.4 Uc (at 55 °C) inrush power in W2000 W (at 20 °C) hold-in power consumption in W42 W at 20 °C heat dissipation42 W operating time70...80 ms closing100...130 ms opening mechanical durability5 Mcycles maximum operating rate600 cyc/h 55 °C compatibility codeLC1F Environment IP degree of protectionIP20 front face with shrouds conforming to IEC 60529IP20 front face with shrouds conforming to VDE 0106 protective treatmentTH ambient air temperature for operation-5…55 °C ambient air temperature for storage-60…80 °C permissible ambient air temperature around the device-40…70 °C operating altitude3000 m without height434 mm width862 mm depth255 mm net weight48 kg Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation EU RoHS DirectiveUnder investigation Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Environmental Disclosure Circularity Profile Contractual warranty Warranty18 months
CatalogueSizeAdd to My DocumentsControl Panel Technical Guide - How to quickly design optimized contactor assemblies (Version 1.1)Tesys catalogue 2019 - 2020 Motor control and protection components (Version 9.2)TeSys catalogue - 2019 - 2020 - chapter B9 high power contactors TeSys F,V, FG, CR1F (Version 7.0)Catalogue TeSys 2019 - Composants pour protection et commande de moteurs (Version 7.1)CADSizeAdd to My DocumentsTeSys F contactor - 4P (4 NO) - AC-1 - <= 440 V 1600 A (Version 1.0)CAD file (on TraceParts) for LC1F7804GD: TeSys F contactor - 4P (4 NO) - AC-1 - <= 440 V 1600 A - coil 125 V DC (Version 2.0)CertificateSizeAdd to My DocumentsInstruction sheetSizeAdd to My DocumentsEnd of Life InformationSizeAdd to My DocumentsProduct Environmental ProfileSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.