View all TeSys F
TeSys F contactor - 4P (4 NO) - AC-1 - <= 440 V 1600 A - coil 110 V DCShow more characteristics >
LC1F7804FD has not been replaced. Please contact your customer care center for more information.
Add to My Products Remove from My Products
The maximum number of products that can be compared is 4
Main rangeTeSys product nameTeSys F product or component typeContactor device short nameLC1F contactor applicationResistive load utilisation categoryAC-1 poles description4P power pole contact composition4 NO [Ue] rated operational voltage<= 1000 V AC 50/60 Hz<= 460 V DC [Ie] rated operational current1600 A (<= 40 °C) at <= 440 V AC AC-1 [Uc] control circuit voltage110 V DC coil typeStandard Complementary [Uimp] rated impulse withstand voltage8 kV overvoltage categoryIII [Ith] conventional free air thermal current1600 A at <= 40 °C rated breaking capacity6240 A conforming to IEC 60947-4-1 [Icw] rated short-time withstand current6250 A <= 40 °C 10 s5600 A <= 40 °C 30 s4600 A <= 40 °C 1 min3000 A <= 40 °C 3 min2200 A <= 40 °C 10 min associated fuse rating800 A aM at <= 440 V1600 A gG at <= 440 V average impedance0.1 mOhm at 50 Hz - Ith 1600 A [Ui] rated insulation voltage1000 V conforming to IEC 60947-4-11500 V conforming to VDE 0110 group C power dissipation per pole250 W AC-1 mounting supportPlate standardsEN 60947-1EN 60947-4-1IEC 60947-1IEC 60947-4-1JIS C8201-4-1 product certificationsABSBVCCCDNVLROS (Lloyds register of shipping)RINARMRoSULCB connections - terminalsControl circuit : screw clamp terminals 2 cable(s) 1...2.5 mm² - cable stiffness: flexible - with cable endControl circuit : screw clamp terminals 1 cable(s) 1...4 mm² - cable stiffness: flexible - without cable endControl circuit : screw clamp terminals 2 cable(s) 1...4 mm² - cable stiffness: flexible - without cable endControl circuit : screw clamp terminals 1 cable(s) 1...4 mm² - cable stiffness: flexible - with cable endControl circuit : screw clamp terminals 1 cable(s) 1...4 mm² - cable stiffness: solid - without cable endControl circuit : screw clamp terminals 2 cable(s) 1...4 mm² - cable stiffness: solid - without cable endPower circuit : bolted connectionPower circuit : bar 2 x (100 x 5 mm) tightening torqueControl circuit : 1.2 N.mPower circuit : 58 N.m control circuit voltage limits0.2...0.4 Uc at 55 °C drop-out0.85...1.1 Uc at 55 °C operational inrush power in W2000 W at 20 °C hold-in power consumption in W42 W at 20 °C heat dissipation42 W operating time100...130 ms opening70...80 ms closing mechanical durability5 Mcycles operating rate600 cyc/h at <= 55 °C Environment IP degree of protectionIP20 front face with shrouds (ordered separately) conforming to IEC 60529IP20 front face with shrouds (ordered separately) conforming to VDE 0106 protective treatmentTH ambient air temperature for operation-5...55 °C ambient air temperature for storage-60...80 °C permissible ambient air temperature around the device-40...70 °C operating altitude3000 m without derating height434 mm width862 mm depth255 mm product weight48 kg Offer Sustainability RoHS (date code: YYWW)Compliant - since 0852 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsCatalogue TeSys 2019 - Chapitre B9 - Contacteurs de forte puissance (Version 4.0)Control Panel Technical Guide - How to quickly design optimized contactor assemblies (Version 1.1)TeSys catalogue - 2019 - 2020 - chapter B9 high power contactors TeSys F,V, FG, CR1F (Version 7.0)Tesys catalogue 2019 - 2020 Motor control and protection components (Version 9.2)CADSizeAdd to My DocumentsTeSys F contactor - 4P (4 NO) - AC-1 - <= 440 V 1600 A (Version 1.0)CAD file (on TraceParts) for LC1F7804FD: TeSys F contactor - 4P (4 NO) - AC-1 - <= 440 V 1600 A - coil 110 V DC (Version 2.0)CertificateSizeAdd to My DocumentsInstruction sheetSizeAdd to My DocumentsEnd of Life InformationSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.