View all TeSys F
TeSys F contactor - 2P (2 NO) - AC-1 - <= 440 V 700 A - coil 415 V ACShow more characteristics >
LC1F5002N7 has not been replaced. Please contact your customer care center for more information.
Add to My Products Remove from My Products
The maximum number of products that can be compared is 4
Main rangeTeSys product nameTeSys F product or component typeContactor device short nameLC1F contactor applicationResistive load utilisation categoryAC-1 poles description2P power pole contact composition2 NO [Ue] rated operational voltage<= 1000 V AC 50/60 Hz<= 460 V DC [Ie] rated operational current700 A (<= 40 °C) at <= 440 V AC AC-1 [Uc] control circuit voltage415 V AC 40...400 Hz Complementary [Uimp] rated impulse withstand voltage8 kV overvoltage categoryIII [Ith] conventional free air thermal current700 A at <= 40 °C rated breaking capacity4000 A conforming to IEC 60947-4-1 [Icw] rated short-time withstand current4200 A <= 40 °C 10 s3200 A <= 40 °C 30 s2400 A <= 40 °C 1 min1500 A <= 40 °C 3 min1200 A <= 40 °C 10 min associated fuse rating500 A aM at <= 440 V800 A gG at <= 440 V average impedance0.18 mOhm at 50 Hz - Ith 700 A [Ui] rated insulation voltage1000 V conforming to IEC 60947-4-11500 V conforming to VDE 0110 group C power dissipation per pole88 W AC-1 mounting supportPlate standardsIEC 60947-1EN 60947-1JIS C8201-4-1EN 60947-4-1IEC 60947-4-1 product certificationsCBRINABVABSLROS (Lloyds register of shipping)ULCCCDNVRMRoS connections - terminalsControl circuit : screw clamp terminals 2 cable(s) 1...2.5 mm² - cable stiffness: flexible - with cable endControl circuit : screw clamp terminals 1 cable(s) 1...4 mm² - cable stiffness: flexible - without cable endControl circuit : screw clamp terminals 2 cable(s) 1...4 mm² - cable stiffness: flexible - without cable endControl circuit : screw clamp terminals 1 cable(s) 1...4 mm² - cable stiffness: flexible - with cable endControl circuit : screw clamp terminals 1 cable(s) 1...4 mm² - cable stiffness: solid - without cable endControl circuit : screw clamp terminals 2 cable(s) 1...4 mm² - cable stiffness: solid - without cable endPower circuit : lugs-ring terminals 2 cable(s) 240 mm²Power circuit : bolted connectionPower circuit : bar 2 x (40 x 5 mm) tightening torquePower circuit : 35 N.mControl circuit : 1.2 N.m control circuit voltage limits0.85...1.1 Uc at 55 °C operational 40...400 Hz0.3...0.5 Uc at 55 °C drop-out 40...400 Hz inrush power in VA1100 VA at 20 °C (cos ϕ 0.9) 40...400 Hz hold-in power consumption in VA18 VA at 20 °C (cos ϕ 0.9) 40...400 Hz heat dissipation18 W operating time100...170 ms opening40...65 ms closing mechanical durability10 Mcycles operating rate2400 cyc/h at <= 55 °C Environment IP degree of protectionIP20 front face with shrouds (ordered separately) conforming to IEC 60529IP20 front face with shrouds (ordered separately) conforming to VDE 0106 protective treatmentTH ambient air temperature for operation-5...55 °C ambient air temperature for storage-60...80 °C permissible ambient air temperature around the device-40...70 °C operating altitude3000 m without derating height238 mm width233 mm depth232 mm product weight9.75 kg Offer Sustainability RoHS (date code: YYWW)Compliant - since 0852 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsCatalogue TeSys 2019 - Chapitre B9 - Contacteurs de forte puissance (Version 4.0)Control Panel Technical Guide - How to quickly design optimized contactor assemblies (Version 1.1)TeSys catalogue - 2019 - 2020 - chapter B9 high power contactors TeSys F,V, FG, CR1F (Version 7.0)Tesys catalogue 2019 - 2020 Motor control and protection components (Version 9.2)CADSizeAdd to My DocumentsCAD file (on TraceParts) for LC1F5002N7: TeSys F contactor - 2P (2 NO) - AC-1 - <= 440 V 700 A - coil 415 V AC (Version 2.0)BrochureSizeAdd to My DocumentsCertificateSizeAdd to My DocumentsInstruction sheetSizeAdd to My DocumentsEnd of Life InformationSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.