View all TeSys F
TeSys F contactor - 2P (2 NO) - AC-1 - <= 440 V 500 A - coil 48 V DCShow more characteristics
LC1F4002ED has not been replaced. Please contact your customer care center for more information.
Add to My Products Remove from My Products
The maximum number of products that can be compared is 4
Main rangeTeSys product nameTeSys F product or component typeContactor device short nameLC1F contactor applicationResistive load utilisation categoryAC-1 poles description2P power pole contact composition2 NO [Ue] rated operational voltage<= 1000 V AC 50/60 Hz<= 460 V DC [Ie] rated operational current500 A (at <40 °C) at <= 440 V AC AC-1 [Uc] control circuit voltage48 V DC coil typeStandard Complementary [Uimp] rated impulse withstand voltage8 kV overvoltage categoryIII [Ith] conventional free air thermal current500 A (at 40 °C) rated breaking capacity3200 A conforming to IEC 60947-4-1 [Icw] rated short-time withstand current3600 A 40 °C - 10 s2400 A 40 °C - 30 s1700 A 40 °C - 1 min1200 A 40 °C - 3 min1000 A 40 °C - 10 min associated fuse rating400 A aM at <= 440 V500 A gG at <= 440 V average impedance0.26 mOhm - Ith 500 A 50 Hz [Ui] rated insulation voltage1000 V conforming to IEC 60947-4-11500 V conforming to VDE 0110 group C power dissipation per pole65 W AC-1 mounting supportPlate standardsEN 60947-4-1EN 60947-1JIS C8201-4-1IEC 60947-4-1IEC 60947-1 product certificationsDNVABSCCCRMRoSCBRINALROS (Lloyds register of shipping)ULBV connections - terminalsControl circuit: screw clamp terminals 1 cable(s) 1…4 mm²flexible without cable endControl circuit: screw clamp terminals 2 cable(s) 1…4 mm²flexible without cable endControl circuit: screw clamp terminals 1 cable(s) 1…4 mm²flexible with cable endControl circuit: screw clamp terminals 2 cable(s) 1…2.5 mm²flexible with cable endControl circuit: screw clamp terminals 1 cable(s) 1…4 mm²solid without cable endControl circuit: screw clamp terminals 2 cable(s) 1…4 mm²solid without cable endPower circuit: bar 2 cable(s) - busbar cross section: 30 x 5 mmPower circuit: lugs-ring terminals 2 cable(s) 150 mm²Power circuit: bolted connection tightening torqueControl circuit: 1.2 N.mPower circuit: 35 N.m control circuit voltage limitsOperational: 0.85...1.1 Uc (at 55 °C)Drop-out: 0.2...0.35 Uc (at 55 °C) inrush power in W1000 W (at 20 °C) hold-in power consumption in W6 W at 20 °C heat dissipation6 W operating time50...60 ms closing45...60 ms opening mechanical durability10 Mcycles maximum operating rate2400 cyc/h 55 °C compatibility codeLC1F Environment IP degree of protectionIP20 front face with shrouds conforming to IEC 60529IP20 front face with shrouds conforming to VDE 0106 protective treatmentTH ambient air temperature for operation-5…55 °C ambient air temperature for storage-60…80 °C permissible ambient air temperature around the device-40…70 °C operating altitude3000 m without height206 mm width213 mm depth219 mm net weight8 kg Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation EU RoHS DirectiveUnder investigation Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Environmental Disclosure Circularity Profile Contractual warranty Warranty18 months
CatalogueSizeAdd to My DocumentsControl Panel Technical Guide - How to quickly design optimized contactor assemblies (Version 1.1)Tesys catalogue 2019 - 2020 Motor control and protection components (Version 9.2)TeSys catalogue - 2019 - 2020 - chapter B9 high power contactors TeSys F,V, FG, CR1F (Version 7.0)Catalogue TeSys 2019 - Composants pour protection et commande de moteurs (Version 7.1)CADSizeAdd to My DocumentsTeSys F contactor - 2P (2 NO) - AC-1 - <= 440 V 500 - 700 A (Version 1.0)CAD file (on TraceParts) for LC1F4002ED: TeSys F contactor - 2P (2 NO) - AC-1 - <= 440 V 500 A - coil 48 V DC (Version 2.0)CertificateSizeAdd to My DocumentsInstruction sheetSizeAdd to My DocumentsEnd of Life InformationSizeAdd to My DocumentsProduct Environmental ProfileSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.