View all TeSys F
View all TeSys F
TeSys F contactor - 3P (3 NO) - AC-3 - <= 440 V 330 A - coil 42 V ACShow more characteristics >
LC1F330D7 has not been replaced. Please contact your customer care center for more information.
Add to My Products Remove from My Products
Main rangeTeSys product nameTeSys F product or component typeContactor device short nameLC1F contactor applicationMotor controlResistive load utilisation categoryAC-1AC-3 poles description3P power pole contact composition3 NO [Ue] rated operational voltage<= 1000 V AC 50/60 Hz<= 460 V DC [Ie] rated operational current400 A (<= 40 °C) at <= 440 V AC AC-1330 A (<= 55 °C) at <= 440 V AC AC-3 motor power kW160 kW at 380...400 V AC 50/60 Hz AC-3200 kW at 500 V AC 50/60 Hz AC-3180 kW at 415 V AC 50/60 Hz AC-3200 kW at 440 V AC 50/60 Hz AC-3160 kW at 1000 V AC 50/60 Hz AC-3100 kW at 220...230 V AC 50/60 Hz AC-359 kW at 400 V AC 50/60 Hz AC-4220 kW at 660...690 V AC 50/60 Hz AC-3 [Uc] control circuit voltage42 V AC 40...400 Hz Complementary [Uimp] rated impulse withstand voltage8 kV overvoltage categoryIII [Ith] conventional free air thermal current400 A at <= 40 °C rated breaking capacity2640 A conforming to IEC 60947-4-1 [Icw] rated short-time withstand current2650 A <= 40 °C 10 s1800 A <= 40 °C 30 s1300 A <= 40 °C 1 min900 A <= 40 °C 3 min750 A <= 40 °C 10 min associated fuse rating400 A aM at <= 440 V500 A gG at <= 440 V average impedance0.28 mOhm at 50 Hz - Ith 400 A [Ui] rated insulation voltage1000 V conforming to IEC 60947-4-11500 V conforming to VDE 0110 group C power dissipation per pole31 W AC-344 W AC-1 mounting supportPlate standardsIEC 60947-1IEC 60947-4-1EN 60947-4-1EN 60947-1JIS C8201-4-1 product certificationsCCCRINACBDNVRMRoSULBVLROS (Lloyds register of shipping)ABS connections - terminalsControl circuit : screw clamp terminals 2 cable(s) 1...2.5 mm² - cable stiffness: flexible - with cable endControl circuit : screw clamp terminals 1 cable(s) 1...4 mm² - cable stiffness: flexible - without cable endControl circuit : screw clamp terminals 2 cable(s) 1...4 mm² - cable stiffness: flexible - without cable endControl circuit : screw clamp terminals 1 cable(s) 1...4 mm² - cable stiffness: flexible - with cable endControl circuit : screw clamp terminals 1 cable(s) 1...4 mm² - cable stiffness: solid - without cable endControl circuit : screw clamp terminals 2 cable(s) 1...4 mm² - cable stiffness: solid - without cable endPower circuit : lugs-ring terminals 1 cable(s) 240 mm²Power circuit : bar 2 x (30 x 5 mm) tightening torquePower circuit : 35 N.mControl circuit : 1.2 N.m control circuit voltage limits0.85...1.1 Uc at 55 °C operational 40...400 Hz0.35...0.55 Uc at 55 °C drop-out 40...400 Hz inrush power in VA650 VA at 20 °C (cos ϕ 0.9) 40...400 Hz hold-in power consumption in VA10 VA at 20 °C (cos ϕ 0.9) 40...400 Hz heat dissipation8 W operating time100...170 ms opening40...65 ms closing mechanical durability10 Mcycles operating rate2400 cyc/h at <= 55 °C Environment IP degree of protectionIP20 front face with shrouds (ordered separately) conforming to IEC 60529IP20 front face with shrouds (ordered separately) conforming to VDE 0106 protective treatmentTH ambient air temperature for operation-5...55 °C ambient air temperature for storage-60...80 °C permissible ambient air temperature around the device-40...70 °C operating altitude3000 m without derating height206 mm width213 mm depth219 mm product weight8.6 kg Offer Sustainability RoHS (date code: YYWW) Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsTesys catalogue 2019 - 2020 Motor control and protection components (Version 9.1)TeSys catalogue - 2019 - 2020 - chapter A2 - open, pre-cabled motor starters (Version 6.0)Catalogue TeSys 2019 - Composants pour protection et commande de moteurs (Version 7.0)CADSizeAdd to My DocumentsBrochureSizeAdd to My DocumentsCertificateSizeAdd to My DocumentsInstruction sheetSizeAdd to My DocumentsDeclaration of conformitySizeAdd to My DocumentsEnd of Life InformationSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.