LC1DGK11B7 is replaced by:
Main rangeTeSys product nameTeSys LC1D.K product or component typeCapacitor duty contactor device short nameLC1DGK contactor applicationPower factor correction poles description3P power pole contact composition3 NO [Ue] rated operational voltage<= 690 V AC 50/60 Hz for power circuit reactive power rating16.7 kvar at 400...440 V AC 50/60 Hz <= 55 °C24 kvar at 660...690 V AC 50/60 Hz <= 55 °C8.5 kvar at 220...240 V AC 50/60 Hz <= 55 °C control circuit typeAC 50/60 Hz [Uc] control circuit voltage24 V AC 50/60 Hz auxiliary contact composition1 NO + 1 NC mounting supportRailPlate standardsVDE 0560IEC 60070NF C 54-100IEC 60831 product certificationsCSAUL connections - terminalsPower circuit : connector 1 cable(s) 2.5 mm² - cable stiffness: flexible - with cable endPower circuit : connector 1 cable(s) 4 mm² - cable stiffness: solid - with cable endPower circuit : connector 2 cable(s) 1.5 mm² - cable stiffness: flexible - with cable endPower circuit : connector 2 cable(s) 4 mm² - cable stiffness: solid - with cable end tightening torquePower circuit : 1.7 N.m - on connector Complementary auxiliary contacts typeType mechanically linked (1 NO + 1 NC) conforming to IEC 60947-5-1Type mirror contact (1 NC) conforming to IEC 60947-4-1 Environment IP degree of protectionIP2x conforming to IEC 60529IP2x conforming to VDE 0106 protective treatmentTH conforming to IEC 60068-2-30 ambient air temperature for operation-5...60 °C ambient air temperature for storage-60...80 °C operating altitude3000 m without derating height130 mm width45 mm depth122 mm product weight0.45 kg Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW)Compliant - since 0950 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
REACh Product environmental profileAvailable
Product Environmental Profile
Product end of life instructionsNeed no specific recycling operations Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.