View all TeSys D
View all TeSys D
TeSys D contactor - 4P(4 NO) - AC-1 - <= 440 V 200 A - 115 V AC 50 Hz coilShow more characteristics >
LC1D1150046FE5 has not been replaced. Please contact your customer care center for more information.
Add to My Products Remove from My Products
The maximum number of products that can be compared is 4
Main rangeTeSys product nameTeSys D product or component typeContactor device short nameLC1D contactor applicationResistive load utilisation categoryAC-1 poles description4P power pole contact composition4 NO [Ue] rated operational voltage<= 460 V DC for power circuit<= 1000 V AC 25...400 Hz for power circuit [Ie] rated operational current200 A (<= 60 °C) at <= 440 V AC AC-1 for power circuit control circuit typeAC 50 Hz [Uc] control circuit voltage115 V AC 50 Hz [Uimp] rated impulse withstand voltageConforming to IEC 60947 overvoltage categoryIII [Ith] conventional free air thermal current200 A at <= 60 °C for power circuit Irms rated making capacity1260 A at 440 V for power circuit conforming to IEC 60947 rated breaking capacity1100 A at 440 V for power circuit conforming to IEC 60947 [Icw] rated short-time withstand current1100 A <= 40 °C 1 s power circuit250 A <= 40 °C 10 min power circuit550 A <= 40 °C 1 min power circuit950 A <= 40 °C 10 s power circuit associated fuse rating200 A gG at <= 690 V coordination type 2 for power circuit250 A gG at <= 690 V coordination type 1 for power circuit average impedance0.6 mOhm at 50 Hz - Ith 200 A for power circuit [Ui] rated insulation voltage1000 V for power circuit conforming to IEC 60947-4-1600 V for power circuit certifications CSA600 V for power circuit certifications UL electrical durability0.8 Mcycles 200 A AC-1 at Ue <= 440 V power dissipation per pole24 W AC-1 safety coverWith mounting supportRailPlate standardsCSA C22.2 No 14EN 60947-4-1EN 60947-5-1IEC 60947-4-1IEC 60947-5-1UL 508 product certificationsDNVBVULCSACCCLROS (Lloyds register of shipping)RINAGOSTGL connections - terminalsPower circuit : bars 1 5 x 25 mmControl circuit : lugs-ring terminals - external diameter: 8 mmPower circuit : lugs-ring terminals - external diameter: 25 mm tightening torqueControl circuit : 1.2 N.m - on lugs-ring terminals - with screwdriver flat Ø 6 mm screw : M3.5Control circuit : 1.2 N.m - on lugs-ring terminals - with screwdriver Philips No 2 screw : M3.5Power circuit : 12 N.m - on lugs-ring terminals hexagonal 13 mm screw : M8Power circuit : 12 N.m - on bars hexagonal 13 mm screw : M8 operating time6...20 ms opening20...50 ms closing safety reliability levelB10d = 1369863 cycles contactor with nominal load conforming to EN/ISO 13849-1B10d = 20000000 cycles contactor with mechanical load conforming to EN/ISO 13849-1 mechanical durability8 Mcycles operating rate2400 cyc/h at <= 60 °C Complementary coil technologyWithout built-in suppressor module control circuit voltage limits0.3...0.6 Uc drop-out at 55 °C, AC 50 Hz0.85...1.1 Uc operational at 55 °C, AC 50 Hz inrush power in VA300 VA at 20 °C (cos ϕ 0.8) 50 Hz hold-in power consumption in VA22 VA at 20 °C (cos ϕ 0.3) 50 Hz heat dissipation3...8 W at 50 Hz Environment IP degree of protectionIP20 front face conforming to IEC 60529 protective treatmentTH conforming to IEC 60068-2-30 pollution degree3 ambient air temperature for operation-5...60 °C ambient air temperature for storage-60...80 °C permissible ambient air temperature around the device-40...70 °C at Uc operating altitude3000 m without derating fire resistance850 °C conforming to IEC 60695-2-1 flame retardanceV1 conforming to UL 94 mechanical robustnessVibrations contactor open 2 Gn, 5...300 HzVibrations contactor closed 4 Gn, 5...300 HzShocks contactor closed 15 Gn for 11 msShocks contactor open 6 Gn for 11 ms height158 mm width155 mm depth115 mm product weight2.86 kg Offer Sustainability RoHS (date code: YYWW)Compliant - since 0742 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
End of Life InformationSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.