Main range of productTeSys D control relayTeSys DTeSys F rangeTeSys product or component typeAuxiliary contact block auxiliary contacts operationInstantaneous pole contact composition2 NC connections - terminalsLugs-ring terminals Complementary mounting locationFront [Ui] rated insulation voltage690 V - conforming to IEC 60947-5-1600 V - certifications CSA600 V - certifications UL [Ue] rated operational voltage690 V AC 25...400 Hz [Ith] conventional free air thermal current10 A at <= 60 °C Irms rated making capacity140 A AC250 A DC permissible short-time rating100 A at 60 °C 1 s120 A at 60 °C 500 ms140 A at 60 °C 100 ms protection typeGG fuse <= 10 A rating according to operational current for Ue <= 690 V associated fuse rating10 A gG IEC 60947-5-1 mechanical durability30 Mcycles minimum switching current5 mA minimum switching voltage17 V non-overlap time1.5 ms on de-energisation (no overlap between NC and NO contact)1.5 ms on energisation (no overlap between NC and NO contact) overlap time1.5 ms insulation resistance> 10 MOhm Environment environmental characteristicNormal environment standardsVDE 0660EN 60947-5-1BS 4794NF C 63-140IEC 60947-5-1 product certificationsULCSA IP degree of protectionIP2x conforming to VDE 0106 protective treatmentTH conforming to IEC 60068 ambient air temperature for operation-40...70 °C ambient air temperature for storage-60...80 °C operating altitude3000 m without derating Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profile Product end of life instructionsNeed no specific recycling operations Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CADSizeAdd to My DocumentsLADN instantaneous auxiliary contact block (Version 1.0)CAD file (on TraceParts) for LADN026: TeSys D - auxiliary contact block - 2 NC - lugs-ring terminals (Version 2.0)CertificateSizeAdd to My DocumentsDeclaration of conformitySizeAdd to My DocumentsProduct Environmental ProfileSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.