Main rangeTeSys product or component typeSerial timer modules device short nameLA4DT poles description3P product compatibility4 poles LC1DT20...DT403 poles LC1D09...D38 Complementary mounting locationTop [Uc] control circuit voltage24...250 V AC 50/60 Hz24...250 V DC control circuit voltage limits0.8...1.1 Uc by mechanical contact [Ui] rated insulation voltage250 V - conforming to IEC 60947-1 connections - terminalsControl circuit : connector 1 cable 1 mm² - cable stiffness: flexible - with cable endControl circuit : connector 1 cable 1 mm² - cable stiffness: solid - with cable endControl circuit : connector 2 cable 2.5 mm² - cable stiffness: flexible - without cable endControl circuit : connector 2 cable 2.5 mm² - cable stiffness: solid - without cable end electrical durability30 Mcycles timer typeOn delay time delay range25...500 s reset time150 ms during time delay50 ms after time delay local signallingIlluminates during time delay by LED [Ures] residual voltage3.3 V product weight0.04 kg Environment standardsIEC 60255-5 product certificationsCSAUL IP degree of protectionIP2x conforming to VDE 0106 protective treatmentTH conforming to IEC 60068 ambient air temperature for operation-25...55 °C permissible ambient air temperature around the device-25...70 °C ambient air temperature for storage-40...80 °C protection typeBuilt-in by varistor heat dissipation2 W at 50/60 Hz immunity to microbreaks10 ms during time delay2 ms after time delay Offer Sustainability RoHS (date code: YYWW) REACh Product end of life instructionsNeed no specific recycling operations Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsCatalogue TeSys 2019 - Composants pour protection et commande de moteurs (Version 7.1)TeSys catalogue - 2019 - 2020 - chapter B8 contactors TeSys SK,K, D, SKGC, GC, GY,GF (Version 7.0)Tesys catalogue 2019 - 2020 Motor control and protection components (Version 9.2)CADSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.