Main rangeCanalis product nameKT product or component typeBusbar trunking busbar descriptionDistribution length device short nameKTC tap-off unit compatibilityPlug-in tap-off unit from Canalis KH device applicationHigh power distribution materialCopper [Ie] rated operational current4000 A at 35 °C polarity3L + N + PE number of tap-off outlets2 nominal output current100...630 A earth conductorReinforced short-circuit levelStandard version length2000 mm provided equipmentTrunking unit Complementary housing materialPolyester film contacts materialCopper [Ue] rated operational voltage1000 V network frequency50/60 Hz [Ui] rated insulation voltage1000 V [Icw] rated short-time withstand current120 kA [Ipk] rated peak withstand current264 kA electrical connectionSliding contact radiated magnetic field2.1 µT thermal stress limit14400 A².s THDI33...100 %, maximum load current: 2500 A15...33 %, maximum load current: 3200 A0...15 %, maximum load current: 4000 A voltage dropWith cos φ =1, 0.001 V at 50 Hz with 1A for 100 m longWith cos φ =0.9, 0.0012 V at 50 Hz with 1A for 100 m longWith cos φ =0.8, 0.0012 V at 50 Hz with 1A for 100 m longWith cos φ =0.7, 0.0012 V at 50 Hz with 1A for 100 m long mounting modeBy hook mounting supportCantilever armPendant installation directionVerticalHorizontal neutral positionRight tap-off unit interval800 mm standardsIEC 61439-1IEC 61439-6 dimension typeFix width140 mm height324 mm colourRAL 9001 : white product weight184 kg linear load92 kg/m Environment IP degree of protectionIP55 conforming to IEC 60529 IK degree of protectionIK08 conforming to IEC 62262 derating factor100 % of In at 0...35 °C95 % of In at 35...40 °C90 % of In at 40...45 °C84 % of In at 45...50 °C79 % of In at 50...55 °C
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsUser guideSizeAdd to My DocumentsCADSizeAdd to My DocumentsDVD Canalis KB-KN-KS-KT-KR_3D CAD simplified (Version 3.0)CAD file (on TraceParts) for ktc4000eh520: CANALIS KT 5X4000CO KH PLUG-IN LENGTH 2M (Version 2.0)
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.