Main rangeCanalis product nameKT product or component typeBusbar trunking busbar descriptionPhase permutation length device short nameKTC device applicationFeeder length materialCopper [Ie] rated operational current3200 A at 35 °C polarity3L + N + PE number of tap-off outlets0 length1000 mm provided equipmentTrunking unitJointing unit Complementary housing materialPolyester film contacts materialCopper [Ue] rated operational voltage1000 V network frequency50/60 Hz [Ui] rated insulation voltage1000 V [Icw] rated short-time withstand current86 kA [Ipk] rated peak withstand current189 kA radiated magnetic field1.6 µT thermal stress limit86 A².s THDI33...100 %, maximum load current: 2000 A15...33 %, maximum load current: 2500 A0...15 %, maximum load current: 3200 A voltage dropWith cos φ =0.8, 0.0015 V at 50 Hz with 1A for 100 m longWith cos φ =1, 0.0013 V at 50 Hz with 1A for 100 m longWith cos φ =0.9, 0.0015 V at 50 Hz with 1A for 100 m longWith cos φ =0.7, 0.0014 V at 50 Hz with 1A for 100 m long mounting modeBy hook mounting supportPendantCantilever arm installation directionHorizontalVertical markingLeft side : N L1 L2 L3Right side : N L3 L2 L1 earth conductorStandard earth short-circuit levelStandard version standardsIEC 61439-1IEC 61439-6 dimension typeFix width140 mm height244 mm colourRAL 9001 : white linear load71 kg/m Environment IP degree of protectionIP55 conforming to IEC 60529 IK degree of protectionIK08 conforming to IEC 62262 derating factor100 % of In at 0...35 °C95 % of In at 35...40 °C90 % of In at 40...45 °C84 % of In at 45...50 °C79 % of In at 50...55 °C Offer Sustainability RoHS (date code: YYWW)Compliant - since 1052 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsUser guideSizeAdd to My DocumentsCADSizeAdd to My DocumentsCAD file (on TraceParts) for ktc3200tp410: KT 4X3200CO PHASES PERMUTA (Version 2.0)DVD Canalis KB-KN-KS-KT-KR_3D CAD simplified (Version 3.0)Instruction sheetSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.