Main rangeCanalis product nameKT product or component typeCenter feeder trunking device short nameKTC device applicationFeeder length supplyDry-type transformer materialCopper [Ie] rated operational current3200 A at 35 °C neutral positionLeft earth conductorReinforced short-circuit levelStandard version provided equipmentTrunking unit Complementary housing materialPolyester film contacts materialCopper [Ue] rated operational voltage1000 V network frequency50/60 Hz [Ui] rated insulation voltage1000 V [Icw] rated short-time withstand current86 kA [Ipk] rated peak withstand current189 kA radiated magnetic field1.6 µT thermal stress limit7396 A².s THDI33...100 %, maximum load current: 2000 A15...33 %, maximum load current: 2500 A0...15 %, maximum load current: 3200 A voltage dropWith cos φ =0.8, 0.0015 V at 50 Hz with 1A for 100 m longWith cos φ =1, 0.0013 V at 50 Hz with 1A for 100 m longWith cos φ =0.9, 0.0015 V at 50 Hz with 1A for 100 m longWith cos φ =0.7, 0.0014 V at 50 Hz with 1A for 100 m long mounting modeBy screws mounting supportPlate polarity3L + N + PE number of tap-off outlets0 standardsIEC 61439-1IEC 61439-6 dimension typeMade to measure connection pitch470...700 mm bar width200 mm depth140 mm height504 mm length1680 mmDirection 1 : 260 mm colourRAL 9001 : white linear load71 kg/m Environment IP degree of protectionIP55 conforming to IEC 60529 IK degree of protectionIK08 conforming to IEC 62262 derating factor100 % of In at 0...35 °C95 % of In at 35...40 °C90 % of In at 40...45 °C84 % of In at 45...50 °C79 % of In at 50...55 °C Offer Sustainability RoHS (date code: YYWW)Compliant - since 0949 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
Product end of life instructionsNeed no specific recycling operations
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsUser guideSizeAdd to My DocumentsCADSizeAdd to My DocumentsCAD file (on TraceParts) for ktc3200el54: KT 5X3200CO FEED UNIT EL N4 (Version 2.0)Instruction sheetSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.