Main rangeCanalis product nameKT product or component typeFlat feeder trunking device short nameKTC device applicationFeeder length supplyOil-immersed transformerSwitchboard materialCopper [Ie] rated operational current2000 A at 35 °C neutral positionRight earth conductorReinforced short-circuit levelReinforced version provided equipmentTrunking unit Complementary housing materialPolyester film contacts materialCopper [Ue] rated operational voltage1000 V network frequency50/60 Hz [Ui] rated insulation voltage1000 V [Icw] rated short-time withstand current110 kA [Ipk] rated peak withstand current242 kA radiated magnetic field0.9 µT thermal stress limit12100 A².s THDI15...33 %, maximum load current: 1600 A0...15 %, maximum load current: 2000 A33...100 %, maximum load current: 1350 A voltage dropWith cos φ =1, 0.0019 V at 50 Hz with 1A for 100 m longWith cos φ =0.9, 0.0022 V at 50 Hz with 1A for 100 m longWith cos φ =0.8, 0.0022 V at 50 Hz with 1A for 100 m longWith cos φ =0.7, 0.0021 V at 50 Hz with 1A for 100 m long mounting modeBy screws mounting supportPlate polarity3L + N + PE number of tap-off outlets0 standardsIEC 61439-1IEC 61439-6 dimension typeMade to measure depth200 mm height350 mm lengthDirection 1 : 235...734 mm colourRAL 9001 : white linear load49 kg/m Environment IP degree of protectionIP55 conforming to IEC 60529 IK degree of protectionIK08 conforming to IEC 62262 derating factor100 % of In at 0...35 °C95 % of In at 35...40 °C90 % of In at 40...45 °C84 % of In at 45...50 °C79 % of In at 50...55 °C Offer Sustainability RoHS (date code: YYWW)Compliant - since 0949 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
Product end of life instructionsNeed no specific recycling operations
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsUser guideSizeAdd to My DocumentsCADSizeAdd to My DocumentsDVD Canalis KB-KN-KS-KT-KR_3D CAD simplified (Version 3.0)CAD file (on TraceParts) for ktc2000er77: KT 5X2000CO FEED UNIT ER N7 (Version 2.0)Instruction sheetSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.