Main rangeCanalis product nameKT product or component typeZed elbow busbar descriptionStandard device short nameKTC device applicationChange direction materialCopper [Ie] rated operational current1350 A at 35 °C polarity3L + N + PE direction change typeDirection 2 : edgewise to horizontalDirection 1 : edgewise to downward operating angle90 ° earth conductorReinforced short-circuit levelReinforced version provided equipmentTrunking unitJointing unit Complementary housing materialPolyester film contacts materialCopper [Ue] rated operational voltage1000 V network frequency50/60 Hz [Ui] rated insulation voltage1000 V [Icw] rated short-time withstand current65 kA [Ipk] rated peak withstand current143 kA radiated magnetic field0.5 µT thermal stress limit4225 A².s THDI15...33 %, maximum load current: 1000 A0...15 %, maximum load current: 1350 A voltage dropWith cos φ =1, 0.0031 V at 50 Hz with 1A for 100 m longWith cos φ =0.9, 0.0034 V at 50 Hz with 1A for 100 m longWith cos φ =0.8, 0.0033 V at 50 Hz with 1A for 100 m longWith cos φ =0.7, 0.0031 V at 50 Hz with 1A for 100 m long neutral positionRight standardsIEC 61439-1IEC 61439-6 dimension typeMade to measure width140 mm heightDirection 2 : 90...579 mm colourWhite : RAL 9001 lengthDirection 1 : 290 mmDirection 3 : 290 mm linear load33 kg/m Environment IP degree of protectionIP55 conforming to IEC 60529 IK degree of protectionIK08 conforming to IEC 62262 derating factor100 % of In at 0...35 °C95 % of In at 35...40 °C90 % of In at 40...45 °C84 % of In at 45...50 °C79 % of In at 50...55 °C Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW)Compliant - since 0949 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
REACh Product environmental profileAvailable Product end of life instructionsNeed no specific recycling operations
CatalogueSizeAdd to My DocumentsUser guideSizeAdd to My DocumentsCADSizeAdd to My DocumentsCAD file (on TraceParts) for ktc1350zc72: KT 5X1350CO EDGEWISE ZED N2 (Version 2.0)
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.