Main rangeCanalis product nameKT product or component typeMultiple elbow busbar descriptionStandard device short nameKTC device applicationChange direction materialCopper [Ie] rated operational current1000 A at 35 °C polarity3L + N + PE direction change typeDirection 1 : flat to rightDirection 2 : edgewise to upward operating angle90 ° earth conductorReinforced short-circuit levelStandard version provided equipmentTrunking unitJointing unit Complementary housing materialPolyester film contacts materialCopper [Ue] rated operational voltage1000 V network frequency50/60 Hz [Ui] rated insulation voltage1000 V [Icw] rated short-time withstand current50 kA [Ipk] rated peak withstand current110 kA radiated magnetic field0.4 µT thermal stress limit2500 A².s THDI0...15 %, maximum load current: 1000 A voltage dropWith cos φ =1, 0.0043 V at 50 Hz with 1A for 100 m longWith cos φ =0.9, 0.0047 V at 50 Hz with 1A for 100 m longWith cos φ =0.8, 0.0046 V at 50 Hz with 1A for 100 m longWith cos φ =0.7, 0.0044 V at 50 Hz with 1A for 100 m long neutral positionLeft standardsIEC 61439-1IEC 61439-6 dimension typeMade to measure width140 mm heightDirection 2 : 195...574 mm colourWhite : RAL 9001 lengthDirection 1 : 300 mmDirection 3 : 275 mm linear load25 kg/m Environment IP degree of protectionIP55 conforming to IEC 60529 IK degree of protectionIK08 conforming to IEC 62262 derating factor100 % of In at 0...35 °C95 % of In at 35...40 °C90 % of In at 40...45 °C84 % of In at 45...50 °C79 % of In at 50...55 °C Offer Sustainability RoHS (date code: YYWW)Compliant - since 0949 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsUser guideSizeAdd to My DocumentsCADSizeAdd to My DocumentsDVD Canalis KB-KN-KS-KT-KR_3D CAD simplified (Version 3.0)CAD file (on TraceParts) for ktc1000cp52: KT 5X1000CO FLAT EDGEWISE N2 (Version 2.0)
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.