Main rangeCanalis product nameKT product or component typeZed elbow busbar descriptionStandard device short nameKTA device applicationChange direction materialAluminium [Ie] rated operational current4000 A at 35 °C polarity3L + N + PE direction change typeDirection 1 : edgewise to upwardDirection 2 : edgewise to horizontal operating angle90 ° earth conductorReinforced short-circuit levelStandard version provided equipmentTrunking unitJointing unit Complementary housing materialPolyester film contacts materialCopper [Ue] rated operational voltage1000 V network frequency50/60 Hz [Ui] rated insulation voltage1000 V [Icw] rated short-time withstand current90 kA [Ipk] rated peak withstand current198 kA radiated magnetic field3 µT thermal stress limit8100 A².s THDI0...15 %, maximum load current: 4000 A voltage dropWith cos φ =1, 0.0015 V at 50 Hz with 1A for 100 m longWith cos φ =0.9, 0.0016 V at 50 Hz with 1A for 100 m longWith cos φ =0.8, 0.0015 V at 50 Hz with 1A for 100 m longWith cos φ =0.7, 0.0015 V at 50 Hz with 1A for 100 m long neutral positionRight standardsIEC 61439-1IEC 61439-6 dimension typeMade to measure width140 mm heightDirection 2 : 90...879 mm colourWhite : RAL 9001 lengthDirection 1 : 440 mmDirection 3 : 440 mm linear load45 kg/m Environment IP degree of protectionIP55 conforming to IEC 60529 IK degree of protectionIK08 conforming to IEC 62262 derating factor100 % of In at 0...35 °C97 % of In at 35...40 °C93 % of In at 40...45 °C90 % of In at 45...50 °C86 % of In at 50...55 °C Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profile Product end of life instructionsNeed no specific recycling operations
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsUser guideSizeAdd to My DocumentsCADSizeAdd to My DocumentsCAD files for kta4000zc51: KT 5X4000AL EDGEWISE ZED N1 (Version 1.0)DVD Canalis KB-KN-KS-KT-KR_3D CAD simplified (Version 3.0)Product Environmental ProfileSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.