Main rangeCanalis product nameKT product or component typeCenter feeder trunking device short nameKTA device applicationFeeder length supplyDry-type transformer materialAluminium [Ie] rated operational current3200 A at 35 °C neutral positionLeft earth conductorReinforced short-circuit levelStandard version provided equipmentTrunking unit Complementary housing materialPolyester film contacts materialCopper [Ue] rated operational voltage1000 V network frequency50/60 Hz [Ui] rated insulation voltage1000 V [Icw] rated short-time withstand current86 kA [Ipk] rated peak withstand current189 kA radiated magnetic field2.1 µT thermal stress limit7396 A².s THDI0...15 %, maximum load current: 3200 A15...33 %, maximum load current: 4000 A voltage dropWith cos φ =1, 0.0018 V at 50 Hz with 1A for 100 m longWith cos φ =0.9, 0.0019 V at 50 Hz with 1A for 100 m longWith cos φ =0.8, 0.0018 V at 50 Hz with 1A for 100 m longWith cos φ =0.7, 0.0017 V at 50 Hz with 1A for 100 m long mounting modeBy screws mounting supportPlate polarity3L + N + PE number of tap-off outlets0 standardsIEC 61439-1IEC 61439-6 dimension typeMade to measure connection pitch470...700 mm bar width200 mm depth140 mm height584 mm length1680 mmDirection 1 : 260 mm colourRAL 9001 : white linear load37 kg/m Environment IP degree of protectionIP55 conforming to IEC 60529 IK degree of protectionIK08 conforming to IEC 62262 derating factor100 % of In at 0...35 °C97 % of In at 35...40 °C93 % of In at 40...45 °C90 % of In at 45...50 °C86 % of In at 50...55 °C Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profileAvailable Product end of life instructionsNeed no specific recycling operations
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsUser guideSizeAdd to My DocumentsCADSizeAdd to My DocumentsDVD Canalis KB-KN-KS-KT-KR_3D CAD simplified (Version 3.0)CAD files for kta3200el54: KT 5X3200AL FEED UNIT EL N4 (Version 1.0)Instruction sheetSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.