Main rangeCanalis product nameKT product or component typeCenter feeder trunking device short nameKTA device applicationFeeder length supplyDry-type transformer materialAluminium [Ie] rated operational current3200 A at 35 °C neutral positionRight earth conductorReinforced short-circuit levelStandard version provided equipmentTrunking unit Complementary housing materialPolyester film contacts materialCopper [Ue] rated operational voltage1000 V network frequency50/60 Hz [Ui] rated insulation voltage1000 V [Icw] rated short-time withstand current86 kA [Ipk] rated peak withstand current189 kA radiated magnetic field2.1 µT thermal stress limit7396 A².s THDI0...15 %, maximum load current: 3200 A15...33 %, maximum load current: 4000 A voltage dropWith cos φ =1, 0.0018 V at 50 Hz with 1A for 100 m longWith cos φ =0.9, 0.0019 V at 50 Hz with 1A for 100 m longWith cos φ =0.8, 0.0018 V at 50 Hz with 1A for 100 m longWith cos φ =0.7, 0.0017 V at 50 Hz with 1A for 100 m long mounting modeBy screws mounting supportPlate polarity3L + N + PE number of tap-off outlets0 standardsIEC 61439-6IEC 61439-1 dimension typeMade to measure connection pitch470...700 mm bar width200 mm depth140 mm height584 mm length1680 mmDirection 1 : 260 mm colourRAL 9001 : white linear load37 kg/m Environment IP degree of protectionIP55 conforming to IEC 60529 IK degree of protectionIK08 conforming to IEC 62262 derating factor100 % of In at 0...35 °C97 % of In at 35...40 °C93 % of In at 40...45 °C90 % of In at 45...50 °C86 % of In at 50...55 °C Offer Sustainability RoHS (date code: YYWW)Compliant - since 0949 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
Product end of life instructionsNeed no specific recycling operations
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsUser guideSizeAdd to My DocumentsCADSizeAdd to My DocumentsDVD Canalis KB-KN-KS-KT-KR_3D CAD simplified (Version 3.0)CAD file (on TraceParts) for kta3200el53: KT 5X3200AL FEED UNIT EL N3 (Version 2.0)Instruction sheetSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.