Main rangeCanalis product nameKT product or component typeSide feeder trunking device short nameKTA device applicationFeeder length supplyDry-type transformer materialAluminium [Ie] rated operational current1600 A at 35 °C neutral positionLeft earth conductorReinforced short-circuit levelStandard version provided equipmentTrunking unit Complementary housing materialPolyester film contacts materialCopper [Ue] rated operational voltage1000 V network frequency50/60 Hz [Ui] rated insulation voltage1000 V [Icw] rated short-time withstand current65 kA [Ipk] rated peak withstand current143 kA radiated magnetic field0.9 µT thermal stress limit4225 A².s THDI0...15 %, maximum load current: 1600 A15...33 %, maximum load current: 2000 A33...100 %, maximum load current: 2500 A voltage dropWith cos φ =1, 0.0037 V at 50 Hz with 1A for 100 m longWith cos φ =0.9, 0.0038 V at 50 Hz with 1A for 100 m longWith cos φ =0.8, 0.0036 V at 50 Hz with 1A for 100 m longWith cos φ =0.7, 0.0034 V at 50 Hz with 1A for 100 m long mounting modeBy screws mounting supportPlate polarity3L + N + PE number of tap-off outlets0 standardsIEC 61439-1IEC 61439-6 dimension typeMade to measure connection pitch470...700 mm bar width200 mm depth140 mm height164 mm length1900 mm colourRAL 9001 : white linear load22 kg/m Environment IP degree of protectionIP55 conforming to IEC 60529 IK degree of protectionIK08 conforming to IEC 62262 derating factor100 % of In at 0...35 °C97 % of In at 35...40 °C93 % of In at 40...45 °C90 % of In at 45...50 °C86 % of In at 50...55 °C Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profile Product end of life instructionsNeed no specific recycling operations
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsUser guideSizeAdd to My DocumentsCADSizeAdd to My DocumentsInstruction sheetSizeAdd to My DocumentsProduct Environmental ProfileSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.