Main rangeCanalis product nameKT product or component typeStraight feeder trunking device short nameKTA device applicationFeeder length supplyOil-immersed transformerSwitchboard materialAluminium [Ie] rated operational current800 A at 35 °C neutral positionRight earth conductorStandard earth short-circuit levelStandard version provided equipmentTrunking unit Complementary housing materialPolyester film contacts materialCopper [Ue] rated operational voltage1000 V network frequency50/60 Hz [Ui] rated insulation voltage1000 V [Icw] rated short-time withstand current31 kA [Ipk] rated peak withstand current64 kA radiated magnetic field0.4 µT thermal stress limit961 A².s THDI0...15 %, maximum load current: 800 A15...33 %, maximum load current: 1000 A33...100 %, maximum load current: 1250 A voltage dropWith cos φ =1, 0.0083 V at 50 Hz with 1A for 100 m longWith cos φ =0.9, 0.0081 V at 50 Hz with 1A for 100 m longWith cos φ =0.8, 0.0076 V at 50 Hz with 1A for 100 m longWith cos φ =0.7, 0.0069 V at 50 Hz with 1A for 100 m long mounting modeBy screws mounting supportPlate polarity3L + N + PE number of tap-off outlets0 standardsIEC 61439-1IEC 61439-6 dimension typeFix connection pitch115 mm width545 mm depth230 mm heightDirection 1 : 235 mm colourRAL 9001 : white linear load13 kg/m Environment IP degree of protectionIP55 conforming to IEC 60529 IK degree of protectionIK08 conforming to IEC 62262 derating factor100 % of In at 0...35 °C97 % of In at 35...40 °C93 % of In at 40...45 °C90 % of In at 45...50 °C86 % of In at 50...55 °C Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profile Product end of life instructionsNeed no specific recycling operations
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsUser guideSizeAdd to My DocumentsCADSizeAdd to My DocumentsInstruction sheetSizeAdd to My DocumentsProduct Environmental ProfileSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.